
EATON-EPDU-MIB DEFINITIONS ::= BEGIN

IMPORTS
	OBJECT-TYPE, NOTIFICATION-TYPE, MODULE-IDENTITY, 
	Counter32, Unsigned32, Integer32, enterprises
		FROM SNMPv2-SMI
	NOTIFICATION-GROUP, OBJECT-GROUP, MODULE-COMPLIANCE
		FROM SNMPv2-CONF
	TEXTUAL-CONVENTION, DateAndTime, DisplayString
		FROM SNMPv2-TC
	pduAgent
		FROM EATON-OIDS;

-- The 3 assignments below are redundant with the one declared in the import file EATON-OIDS.txt
-- because of the compatibility with some SNMP host software that do not support manufacturer import files.
-- Take care not to diverge from the import file.
eaton OBJECT IDENTIFIER ::= { enterprises 534 }
products OBJECT IDENTIFIER ::= { eaton 6  }
pduAgent OBJECT IDENTIFIER ::= { products 6  }

eatonEpdu MODULE-IDENTITY
	LAST-UPDATED "201805301500Z"
	ORGANIZATION 
		"Eaton Corporation"
	CONTACT-INFO 
		"www.eaton.com/epdu"
	DESCRIPTION 
		"The MIB module for Eaton ePDUs (Enclosure Power Distribution Units)."

	REVISION "201805301500Z"
	DESCRIPTION 
		"- Add information about architecture of the ePDU.
		- Add outlet automatic shutoff."

	REVISION "201709111200Z"
	DESCRIPTION 
		"- Add physical name for input, outlet and gang.
		- Add friendly name for input.
		- Add input identification for outlet.
		- Add the nominal power for ePDU input.
		- Add a new outlet type sdg300 (31)."

	REVISION "201704201200Z"
	DESCRIPTION 
		"Add color codes for each input and group. Color codes are decimal values."

	REVISION "201502231200Z"
	DESCRIPTION 
		"Fix compatibility with some SNMP host software by adding some assignments."

	REVISION "201409291200Z"
	DESCRIPTION 
		"Added outletControlSwitchable and outletControlShutoffDelay object."

	REVISION "201312181200Z"
	DESCRIPTION 
		"Added notifyStrappingStatus and strappingStatus object."

    REVISION "201309021200Z"
    DESCRIPTION
        "- Add values for commInterface : ftp (4), xml (5)"

    REVISION "201305291200Z"
    DESCRIPTION
        "- Edited values for outletType: removed nema51520(21); added nemaL715(29), rf203p277 (30)"

	REVISION "201302211200Z"
	DESCRIPTION 
		"- Added unit objects : unitType.
		- Added input objects : inputCurrentCrestFactor, inputCurrentPercentLoad, inputPowerFactor, inputVAR, inputPlugType.
		- Added gang objects : groupCurrentCrestFactor, groupCurrentPercentLoad, groupPowerFactor, groupVAR.
		- Added outlet objects : outletCurrentCrestFactor, outletCurrentPercentLoad, outletPowerFactor, outletVAR."

	REVISION "201111211200Z"
	DESCRIPTION 
		"- Added notifyGroupBreakerStatus object.
		 - Renamed groupStatus object to groupBreakerStatus.  This object had not yet
		             been implemented so there is no user impact. 
		 - Updated descriptions for inputWhTimer, groupWhTimer, and outletWhTimer."

	REVISION "201110241200Z"
	DESCRIPTION 
		"- Added notifyBootUp object.
		           - Added outletType object.
		           - Updated description for all lower and upper thresholds to indicate that
		             a value of -1 indicates that it is not supported by a particular ePDU model.
		           - Updated descriptions for inputVA, inputWatts, groupVA, groupWatts, outletVA,
		             outletWatts to indicate that a value of -1 indicates that it is not
		             supported by a particular ePDU model.
		           - Added a note to unit, group, and outlet level control command objects
		             indicating that some products (mainly with part numbers that begin with IPV
		             or IPC) do not support delayed outlet control commands and will reply with
		             an error if a command value is written that is > 0.
		           - Corrected description for inputType.
		           - Added a UnixTimeStamp Textual Convention and changed the SYNTAX of
		             inputWhTimer, groupWhTimer, and outletWhTimer to use it.
		           - Updated the contact info to reference the ePDU website."

	REVISION "201102071529Z"
	DESCRIPTION 
		"Initial release."
::= { pduAgent 7 }

UnixTimeStamp ::= TEXTUAL-CONVENTION
	STATUS     current
	DESCRIPTION 
		"Unix time stamp.  Measured in seconds since January 1, 1970."
	SYNTAX  Counter32


-- eatonEpdu { iso org(3) dod(6) internet(1) private(4)
--       enterprises(1) eaton(534) products(6) pduAgent(6) (7) }

notifications        OBJECT IDENTIFIER ::= { eatonEpdu 0 }
units                OBJECT IDENTIFIER ::= { eatonEpdu 1 }
inputs               OBJECT IDENTIFIER ::= { eatonEpdu 3 }
groups               OBJECT IDENTIFIER ::= { eatonEpdu 5 }
outlets              OBJECT IDENTIFIER ::= { eatonEpdu 6 }
environmental        OBJECT IDENTIFIER ::= { eatonEpdu 7 }
conformance          OBJECT IDENTIFIER ::= { eatonEpdu 25 }
objectGroups         OBJECT IDENTIFIER ::= { conformance 5 }

notifyUserLogin  NOTIFICATION-TYPE
	OBJECTS { userName, 
		commInterface }
	STATUS     current
	DESCRIPTION 
		"Sent whenever a user logs in."
	::= { notifications 1 }

notifyUserLogout  NOTIFICATION-TYPE
	OBJECTS { userName, 
		commInterface }
	STATUS     current
	DESCRIPTION 
		"Sent whenever a user logs out."
	::= { notifications 2 }

notifyFailedLogin  NOTIFICATION-TYPE
	OBJECTS { userName, 
		commInterface }
	STATUS     current
	DESCRIPTION 
		"Sent when someone attempts to log in and fails.  On some models, may be
		      sent after three failed login attempts."
	::= { notifications 3 }

notifyBootUp  NOTIFICATION-TYPE
	OBJECTS { strappingIndex }
	STATUS     current
	DESCRIPTION 
		"Sent whenever an ePDU finishes booting up (hard or soft reboot)."
	::= { notifications 4 }

notifyInputVoltageThStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		inputIndex, 
		inputVoltageIndex, 
		inputVoltage, 
		inputVoltageThStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever an input voltage threshold status changes."
	::= { notifications 11 }

notifyInputCurrentThStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		inputIndex, 
		inputCurrentIndex, 
		inputCurrent, 
		inputCurrentThStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever an input current threshold status changes."
	::= { notifications 12 }

notifyInputFrequencyStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		inputIndex, 
		inputFrequency, 
		inputFrequencyStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever the input frequency status changes."
	::= { notifications 13 }

notifyGroupVoltageThStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		groupIndex, 
		groupVoltage, 
		groupVoltageThStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever a group voltage threshold status changes."
	::= { notifications 21 }

notifyGroupCurrentThStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		groupIndex, 
		groupCurrent, 
		groupCurrentThStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever a group current threshold status changes."
	::= { notifications 22 }

notifyGroupBreakerStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		groupIndex, 
		groupBreakerStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever a group status changes to indicate whether the circuit
		          breaker is on or off."
	::= { notifications 23 }

notifyOutletVoltageThStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		outletIndex, 
		outletVoltage, 
		outletVoltageThStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever an outlet voltage threshold status changes."
	::= { notifications 31 }

notifyOutletCurrentThStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		outletIndex, 
		outletCurrent, 
		outletCurrentThStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever an outlet current threshold status changes."
	::= { notifications 32 }

notifyOutletControlStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		outletIndex, 
		outletControlStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever an outlet state On / Off changes."
	::= { notifications 33 }

notifyTemperatureThStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		temperatureIndex, 
		temperatureValue, 
		temperatureThStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever a temperature threshold status changes."
	::= { notifications 41 }

notifyHumidityThStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		humidityIndex, 
		humidityValue, 
		humidityThStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever a humidity threshold status changes."
	::= { notifications 42 }

notifyContactState  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		contactIndex, 
		contactState }
	STATUS     current
	DESCRIPTION 
		"Sent whenever a contact sensor state changes."
	::= { notifications 43 }

notifyProbeStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		temperatureIndex, 
		temperatureProbeStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever the environment probe status changes."
	::= { notifications 44 }

notifyCommunicationStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		communicationStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever the PDU communication status changes."
	::= { notifications 51 }

notifyInternalStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		internalStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever the PDU internal status changes."
	::= { notifications 52 }

notifyTest  NOTIFICATION-TYPE
	STATUS     current
	DESCRIPTION 
		"Sent whenever the trap test feature is used by the communication card."
	::= { notifications 53 }

notifyStrappingStatus  NOTIFICATION-TYPE
	OBJECTS { strappingIndex, 
		strappingStatus }
	STATUS     current
	DESCRIPTION 
		"Sent whenever the strapping communication status changes."
	::= { notifications 54 }

unitsPresent  OBJECT-TYPE
	SYNTAX     DisplayString
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Each unit is identified by a Strapping Index.  This object returns a comma-delimited list of the
		Strapping Indexes of all units present in the strapping group.  For example, if units 0, 1, 5,
		and 7 are present, this value will be '0,1,5,7'.  For units that do not support strapping,
		a Strapping Index of '0' is assumed."
	::= { units 1 }

unitTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF UnitEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of units.  In most cases this list will only contain one entry.
		      However, some units have a 'strapping' feature which allow units to be
		      daisy-chained together such that all of them can be accessed through
		      the SNMP interface of the master.  If strapping is enabled, the 
		      strapping indexes of the units that can be accessed will be listed in the
		      unitsPresent object."
	::= { units 2 }

unitEntry  OBJECT-TYPE
	SYNTAX 	UnitEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a PDU."
	INDEX { strappingIndex }
	::= { unitTable 1 }

UnitEntry ::= SEQUENCE {
	strappingIndex
		Integer32,
	productName
		OCTET STRING,
	partNumber
		OCTET STRING,
	serialNumber
		OCTET STRING,
	firmwareVersion
		OCTET STRING,
	unitName
		OCTET STRING,
	lcdControl
		INTEGER,
	clockValue
		DateAndTime,
	temperatureScale
		INTEGER,
	unitType
		INTEGER,
	systemType
		INTEGER,
	inputCount
		Integer32,
	groupCount
		Integer32,
	outletCount
		Integer32,
	temperatureCount
		Integer32,
	humidityCount
		Integer32,
	contactCount
		Integer32,
	communicationStatus
		INTEGER,
	internalStatus
		INTEGER,
	strappingStatus
		INTEGER,
	userName
		OCTET STRING,
	commInterface
		INTEGER
}

strappingIndex  OBJECT-TYPE
	SYNTAX     Integer32 (0..23)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"For units that support 'strapping' functionality, this will be a unique
		      value for each unit.  If units do not support 'strapping', this will
		      always be '0'."
	::= { unitEntry 1 }

productName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(1..127))
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Name of the product."
	::= { unitEntry 2 }

partNumber  OBJECT-TYPE
	SYNTAX     OCTET STRING
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Part number of the unit."
	::= { unitEntry 3 }

serialNumber  OBJECT-TYPE
	SYNTAX     OCTET STRING
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Serial number of the unit."
	::= { unitEntry 4 }

firmwareVersion  OBJECT-TYPE
	SYNTAX     OCTET STRING
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Firmware version."
	::= { unitEntry 5 }

unitName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(1..63))
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Descriptive name for the unit."
	::= { unitEntry 6 }

lcdControl  OBJECT-TYPE
	SYNTAX     INTEGER {
		notApplicable (0),
		lcdScreenOff (1),
		lcdKeyLock (2),
		lcdScreenOffAndKeyLock (3)
	}
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Control the local LCD."
	::= { unitEntry 7 }

clockValue  OBJECT-TYPE
	SYNTAX     DateAndTime
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Clock value.  This could be from either a real-time clock (in which case
		      it is likely writeable) or from a time server via NTP (probably read-only)."
	::= { unitEntry 8 }

temperatureScale  OBJECT-TYPE
	SYNTAX     INTEGER {
		celsius (0),
		fahrenheit (1)
	}
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Scale used to return temperature objects."
	::= { unitEntry 9 }

unitType  OBJECT-TYPE
	SYNTAX     INTEGER {
		unknown (0),
		switched (1),
		advancedMonitored (2),
		managed (3),
		monitored (4),
		basic (5),
		inlineMonitored (6)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Technical capabilities of the PDU.  Functionality is as follows:
            Monitored (MI) - input and usually section/group monitoring.
            Advanced Monitored (AM) - input, section/group, and outlet monitoring.
            Switched (SW) - input and section/group monitoring, outlet switching.
            Basic (BA) - no communication card.
            Inline Monitored (IL) - input and usually one section/group monitoring."
	::= { unitEntry 10 }

systemType  OBJECT-TYPE
	SYNTAX     INTEGER {
		unknown (0),
		g3ePDU (1),
		g3HDePDU (2)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Architecture of the ePDU electronic."
	::= { unitEntry 11 }
  
inputCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Number of inputs on this ePDU."
	::= { unitEntry 20 }

groupCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Number of groups on this ePDU.  Groups include breakers, outlet sections,
		      and user-defined groups."
	::= { unitEntry 21 }

outletCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Number of outlets on this ePDU."
	::= { unitEntry 22 }

temperatureCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Max number of temperature measurements on this ePDU."
	::= { unitEntry 23 }

humidityCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Max number of humidity measurements on this ePDU."
	::= { unitEntry 24 }

contactCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Max number of contact sensors on this ePDU."
	::= { unitEntry 25 }

communicationStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		communicationLost (1)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the internal communication with the PDU."
	::= { unitEntry 30 }

internalStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		internalFailure (1)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the internal failure inside the PDU."
	::= { unitEntry 31 }

strappingStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		communicationLost (1)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the external communication with a strapping unit."
	::= { unitEntry 32 }

userName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(0..31))
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"Username used to log into the PDU."
	::= { unitEntry 40 }

commInterface  OBJECT-TYPE
	SYNTAX     INTEGER {
		serial (0),
		usb (1),
		telnet (2),
		web (3),
		ftp (4),
		xml (5)
	}
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"Communications interface used to log into the PDU."
	::= { unitEntry 41 }

unitControlTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF UnitControlEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of units that have controllable outlets."
	::= { units 3 }

unitControlEntry  OBJECT-TYPE
	SYNTAX 	UnitControlEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a PDU which has controllable outlets."
	INDEX { strappingIndex }
	::= { unitControlTable 1 }

UnitControlEntry ::= SEQUENCE {
	unitControlOffCmd
		Integer32,
	unitControlOnCmd
		Integer32
}

unitControlOffCmd  OBJECT-TYPE
	SYNTAX     Integer32 (-1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Unit-level outlet control command.
		
		Once the command is issued, outlets will turn Off.
		0-n : Time in seconds until the outlet Sequence Off command is issued
		-1 : Cancel a pending unit-level Off command 
		
		When read, returns -1 if no command is pending, or the current downcount in seconds of a pending command.
		          
		          Certain ePDUs (mainly those with part numbers beginning with IPV or IPC) do not support delayed control
		          commands.  These will respond with an error if a command value of > 0 is written to this object."
	::= { unitControlEntry 2 }

unitControlOnCmd  OBJECT-TYPE
	SYNTAX     Integer32 (-1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Unit-level outlet control command.
		
		Once the command is issued, outlets will turn On according to their outletControlSequenceDelay value.
		0-n : Time in seconds until the outlet Sequence On command is issued
		-1 : Cancel a pending unit-level On command 
		
		When read, returns -1 if no command is pending, or the current downcount in seconds of a pending command.
		          
		          Certain ePDUs (mainly those with part numbers beginning with IPV or IPC) do not support delayed control
		          commands.  These will respond with an error if a command value of > 0 is written to this object."
	::= { unitControlEntry 3 }

inputTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF InputEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"List of inputs to the PDU."
	::= { inputs 1 }

inputEntry  OBJECT-TYPE
	SYNTAX 	InputEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a particular input."
	INDEX { strappingIndex, 
		inputIndex }
	::= { inputTable 1 }

InputEntry ::= SEQUENCE {
	inputIndex
		Integer32,
	inputType
		INTEGER,
	inputFrequency
		Integer32,
	inputFrequencyStatus
		INTEGER,
	inputVoltageCount
		Integer32,
	inputCurrentCount
		Integer32,
	inputPowerCount
		Integer32,
	inputPlugType
		INTEGER,
	inputFeedColor
		Unsigned32,
	inputFeedName
		OCTET STRING
}

inputIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..2)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"A unique value for each input.  Its value ranges from 1 to inputCount."
	::= { inputEntry 1 }

inputType  OBJECT-TYPE
	SYNTAX     INTEGER {
		singlePhase (1),
		splitPhase (2),
		threePhaseDelta (3),
		threePhaseWye (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Type of input - single phase, split phase, three phase delta, or three
		phase wye."
	::= { inputEntry 2 }

inputFrequency  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Units are 0.1 Hz; divide by ten to get Hz."
	::= { inputEntry 3 }

inputFrequencyStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		outOfRange (1)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured input frequency relative to the nominal frequency and the admitted tolerance."
	::= { inputEntry 4 }

inputVoltageCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Number of input voltage measurements on this ePDU."
	::= { inputEntry 5 }

inputCurrentCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Number of input current measurements on this ePDU."
	::= { inputEntry 6 }

inputPowerCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Number of rows in the inputPowerTable."
	::= { inputEntry 7 }

inputPlugType  OBJECT-TYPE
	SYNTAX     INTEGER {
		other1Phase (100),
        other2Phase (200),
        other3Phase (300),
        iecC14Inlet (101),
        iecC20Inlet (102),
        iec316P6 (103),
        iec332P6 (104),
        iec360P6 (105),
        iecC14Plug (106),
        iecC20Plug (107),
        nema515 (120),
        nemaL515 (121),
        nema520 (122),
        nemaL520 (123),
        nema615 (124),
        nemaL615 (125),
        nemaL530 (126),
        nema620 (127),
        nemaL620 (128),
        nemaL630 (129),
        cs8265 (130),
        french (150),
        schuko (151),
        uk (152),
        nemaL1420 (201),
        nemaL1430 (202),
        iec516P6 (301),
        iec460P9 (302),
        iec560P9 (303),
        iec532P6 (304),
        iec563P6 (306),
        nemaL1520 (320),
        nemaL2120 (321),
        nemaL1530 (322),
        nemaL2130 (323),
        cs8365 (324),
        nemaL2220 (325),
        nemaL2230 (326),
        bladeUps208V (350),
        bladeUps400V (351)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Identifies which plug is on the input."
	::= { inputEntry 8 }

inputFeedColor  OBJECT-TYPE
	SYNTAX     Unsigned32 (0..16777215)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Color code of the input feed."
	::= { inputEntry 9 }

inputFeedName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(1..31))
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"A descriptive name for the input."
	::= { inputEntry 10 }




inputVoltageTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF InputVoltageEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of input voltage measurements.  The number of entries
		      is given by inputVoltageCount."
	::= { inputs 2 }

inputVoltageEntry  OBJECT-TYPE
	SYNTAX 	InputVoltageEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a particular input voltage measurement."
	INDEX { strappingIndex, 
		inputIndex, 
		inputVoltageIndex }
	::= { inputVoltageTable 1 }

InputVoltageEntry ::= SEQUENCE {
	inputVoltageIndex
		Integer32,
	inputVoltageMeasType
		INTEGER,
	inputVoltage
		Integer32,
	inputVoltageThStatus
		INTEGER,
	inputVoltageThLowerWarning
		Integer32,
	inputVoltageThLowerCritical
		Integer32,
	inputVoltageThUpperWarning
		Integer32,
	inputVoltageThUpperCritical
		Integer32
}

inputVoltageIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..3)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"A unique value for each input voltage measurement.  Its value ranges 
		      from 1 to inputVoltageCount."
	::= { inputVoltageEntry 1 }

inputVoltageMeasType  OBJECT-TYPE
	SYNTAX     INTEGER {
		singlePhase (1),
		phase1toN (2),
		phase2toN (3),
		phase3toN (4),
		phase1to2 (5),
		phase2to3 (6),
		phase3to1 (7)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Value indicates what input voltage is being measured in this table row - single phase
		voltage, phase 1 to neutral, phase 2 to neutral, phase 3 to neutral, phase 1 to phase 2,
		phase 2 to phase 3, or phase 3 to phase 1."
	::= { inputVoltageEntry 2 }

inputVoltage  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input voltage measurement value.  Units are millivolts."
	::= { inputVoltageEntry 3 }

inputVoltageThStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		lowWarning (1),
		lowCritical (2),
		highWarning (3),
		highCritical (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured input voltage relative to the configured thresholds."
	::= { inputVoltageEntry 4 }

inputVoltageThLowerWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower warning threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { inputVoltageEntry 5 }

inputVoltageThLowerCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower critical threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { inputVoltageEntry 6 }

inputVoltageThUpperWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper warning threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { inputVoltageEntry 7 }

inputVoltageThUpperCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper critical threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { inputVoltageEntry 8 }



inputCurrentTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF InputCurrentEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of input current measurements.  The number of entries
		      is given by inputCurrentCount."
	::= { inputs 3 }

inputCurrentEntry  OBJECT-TYPE
	SYNTAX 	InputCurrentEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a particular input current measurement."
	INDEX { strappingIndex, 
		inputIndex, 
		inputCurrentIndex }
	::= { inputCurrentTable 1 }

InputCurrentEntry ::= SEQUENCE {
	inputCurrentIndex
		Integer32,
	inputCurrentMeasType
		INTEGER,
	inputCurrentCapacity
		Integer32,
	inputCurrent
		Integer32,
	inputCurrentThStatus
		INTEGER,
	inputCurrentThLowerWarning
		Integer32,
	inputCurrentThLowerCritical
		Integer32,
	inputCurrentThUpperWarning
		Integer32,
	inputCurrentThUpperCritical
		Integer32,
	inputCurrentCrestFactor
		Integer32,
	inputCurrentPercentLoad
		Integer32,
	inputPhaseDesignator
		DisplayString
}

inputCurrentIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..4)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"A unique value for each input current measurement.  Its value ranges
		      from 1 to inputCurrentCount."
	::= { inputCurrentEntry 1 }

inputCurrentMeasType  OBJECT-TYPE
	SYNTAX     INTEGER {
		singlePhase (1),
		neutral (2),
		phase1 (3),
		phase2 (4),
		phase3 (5)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Which input wire is being measured in this table row - single phase, neutral, phase 1,
		phase 2, or phase 3."
	::= { inputCurrentEntry 2 }

inputCurrentCapacity  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Rated current capacity of the input.  A negative value indicates that
		the hardware current capacity is unknown.  Units are milliamps."
	::= { inputCurrentEntry 3 }

inputCurrent  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input current measurement value.  Units are milliamps."
	::= { inputCurrentEntry 4 }

inputCurrentThStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		lowWarning (1),
		lowCritical (2),
		highWarning (3),
		highCritical (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured input current relative to the configured thresholds."
	::= { inputCurrentEntry 5 }

inputCurrentThLowerWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower warning threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { inputCurrentEntry 6 }

inputCurrentThLowerCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower critical threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { inputCurrentEntry 7 }

inputCurrentThUpperWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper warning threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { inputCurrentEntry 8 }

inputCurrentThUpperCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper critical threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { inputCurrentEntry 9 }

inputCurrentCrestFactor  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Current crest factor.  Units are in milli, for example a crest factor of
                  1.414 will be returned as 1414.  A negative value indicates
		          that this object is not available."
	::= { inputCurrentEntry 10 }

inputCurrentPercentLoad  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Current percent load, based on the rated current capacity.  Units are
                  percentage, for example 80% will be returned as 80.  A negative
                  value indicates that this object is not available."
	::= { inputCurrentEntry 11 }

inputPhaseDesignator  OBJECT-TYPE
	SYNTAX     DisplayString (SIZE(2..4))
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Alphanumeric physical name for the input."
	::= { inputCurrentEntry 12 }




inputPowerTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF InputPowerEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of input power measurements.  The number of entries
		      is given by inputPowerCount."
	::= { inputs 4 }

inputPowerEntry  OBJECT-TYPE
	SYNTAX 	InputPowerEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for an input power measurement."
	INDEX { strappingIndex, 
		inputIndex, 
		inputPowerIndex }
	::= { inputPowerTable 1 }

InputPowerEntry ::= SEQUENCE {
	inputPowerIndex
		Integer32,
	inputPowerMeasType
		INTEGER,
	inputVA
		Integer32,
	inputWatts
		Integer32,
	inputWh
		Unsigned32,
	inputWhTimer
		UnixTimeStamp,
	inputPowerFactor
		Integer32,
	inputVAR
		Integer32
}

inputPowerIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..12)
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A unique value for each input power measurement.  Its value ranges
		      from 1 to inputPowerCount."
	::= { inputPowerEntry 1 }

inputPowerMeasType  OBJECT-TYPE
	SYNTAX     INTEGER {
		unknown (0),
		phase1 (1),
		phase2 (2),
		phase3 (3),
		total (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Value indicates what is being measured in this table row."
	::= { inputPowerEntry 2 }

inputVA  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input VA value.  Units are VA.  A negative value indicates
		          that this object is not available."
	::= { inputPowerEntry 3 }

inputWatts  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input Watts value.  Units are Watts.  A negative value indicates
		          that this object is not available."
	::= { inputPowerEntry 4 }

inputWh  OBJECT-TYPE
	SYNTAX     Unsigned32 (0..4294967295)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Units are Watt-hours.  This object is writable so that it can be reset to 0.  When it is
		written to, the inputWhTimer will be reset updated as well."
	::= { inputPowerEntry 5 }

inputWhTimer  OBJECT-TYPE
	SYNTAX     UnixTimeStamp
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Timestamp of when input Watt-hours (inputWh) was last reset."
	::= { inputPowerEntry 6 }

inputPowerFactor  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input PF value.  Units are in thousandths, for example a power factor
                  of 0.958 would be returned as 958, and 0.92 would be returned 
		          as 920.  A negative value indicates that this object is not
                  available."
	::= { inputPowerEntry 7 }

inputVAR  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input VAR value.  Units are VAR.  A negative value indicates
		          that this object is not available."
	::= { inputPowerEntry 8 }





inputTotalPowerTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF InputTotalPowerEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of total input power measurements."
	::= { inputs 5 }

inputTotalPowerEntry  OBJECT-TYPE
	SYNTAX 	InputTotalPowerEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a total input power measurement."
	INDEX { strappingIndex, 
		inputIndex }
	::= { inputTotalPowerTable 1 }

InputTotalPowerEntry ::= SEQUENCE {
	inputTotalVA
		Integer32,
	inputTotalWatts
		Integer32,
	inputTotalWh
		Unsigned32,
	inputTotalWhTimer
		UnixTimeStamp,
	inputTotalPowerFactor
		Integer32,
	inputTotalVAR
		Integer32,
	inputPowerCapacity
		Integer32
}

inputTotalVA  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input VA value.  Units are VA.  A negative value indicates
		          that this object is not available."
	::= { inputTotalPowerEntry 3 }

inputTotalWatts  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input Watts value.  Units are Watts.  A negative value indicates
		          that this object is not available."
	::= { inputTotalPowerEntry 4 }

inputTotalWh  OBJECT-TYPE
	SYNTAX     Unsigned32 (0..4294967295)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Units are Watt-hours.  This object is writable so that it can be reset to 0.  When it is
		written to, the inputWhTimer will be reset updated as well."
	::= { inputTotalPowerEntry 5 }

inputTotalWhTimer  OBJECT-TYPE
	SYNTAX     UnixTimeStamp
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Timestamp of when input Watt-hours (inputWh) was last reset."
	::= { inputTotalPowerEntry 6 }

inputTotalPowerFactor  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input PF value.  Units are in thousandths, for example a power factor
                  of 0.958 would be returned as 958, and 0.92 would be returned 
		          as 920.  A negative value indicates that this object is not
                  available."
	::= { inputTotalPowerEntry 7 }

inputTotalVAR  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An input VAR value.  Units are VAR.  A negative value indicates
		          that this object is not available."
	::= { inputTotalPowerEntry 8 }

inputPowerCapacity  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Typical power capacity of the input.  A negative value indicates that
		the hardware current capacity is unknown."
	::= { inputTotalPowerEntry 9 }




groupTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF GroupEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of groups.  The number of entries is given by groupCount."
	::= { groups 1 }

groupEntry  OBJECT-TYPE
	SYNTAX 	GroupEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a particular group."
	INDEX { strappingIndex, 
		groupIndex }
	::= { groupTable 1 }

GroupEntry ::= SEQUENCE {
	groupIndex
		Integer32,
	groupID
		DisplayString,
	groupName
		OCTET STRING,
	groupType
		INTEGER,
	groupBreakerStatus
		INTEGER,
	groupChildCount
		Integer32,
	groupColor
		Unsigned32,
	groupDesignator
		DisplayString,
	groupInputIndex
		Integer32
}

groupIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..64)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"A unique value for each group.  Its value ranges from 1 to groupCount."
	::= { groupEntry 1 }

groupID  OBJECT-TYPE
	SYNTAX     DisplayString (SIZE(2..4))
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Alphanumeric designator for the group.  This value may be written
		      on the face of the unit."
	::= { groupEntry 2 }

groupName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(1..31))
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"A descriptive name for the group."
	::= { groupEntry 3 }

groupType  OBJECT-TYPE
	SYNTAX     INTEGER {
		unknown (0),
		breaker1pole (1),
		breaker2pole (2),
		breaker3pole (3),
		outletSection (4),
		userDefined (5)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"The type of the group."
	::= { groupEntry 4 }

groupBreakerStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		notApplicable (0),
		breakerOn (1),
		breakerOff (2)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Only applicable to breaker-groups.  Indicates whether a breaker is turned
		      off or on."
	::= { groupEntry 5 }

groupChildCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Number of children for this group."
	::= { groupEntry 6 }

groupColor  OBJECT-TYPE
	SYNTAX     Unsigned32 (0..16777215)
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Background color code of the group. Color codes are decimal values."
	::= { groupEntry 7 }

groupDesignator  OBJECT-TYPE
	SYNTAX     DisplayString (SIZE(2..4))
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Alphanumeric physical name for the group.  This value may be written
		      on the face of the unit."
	::= { groupEntry 8 }

groupInputIndex  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Identifies the input on which the group is connected."
	::= { groupEntry 9 }



groupChildTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF GroupChildEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of children for this group.  For example, this table will link
		      to all of the outlets that are contained in a particular group."
	::= { groups 2 }

groupChildEntry  OBJECT-TYPE
	SYNTAX 	GroupChildEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a particular child."
	INDEX { strappingIndex, 
		groupIndex, 
		groupChildIndex }
	::= { groupChildTable 1 }

GroupChildEntry ::= SEQUENCE {
	groupChildIndex
		Integer32,
	groupChildType
		INTEGER,
	groupChildOID
		OBJECT IDENTIFIER
}

groupChildIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..32)
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A unique value for each child.  Its value ranges from 1 to groupChildCount."
	::= { groupChildEntry 1 }

groupChildType  OBJECT-TYPE
	SYNTAX     INTEGER {
		unknown (0),
		section (2),
		custom (3),
		outlet (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"The type of the child."
	::= { groupChildEntry 2 }

groupChildOID  OBJECT-TYPE
	SYNTAX     OBJECT IDENTIFIER
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Object ID of a child object."
	::= { groupChildEntry 3 }

groupVoltageTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF GroupVoltageEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of group voltage measurements.  There can be only one voltage
		      measurement for each group."
	::= { groups 3 }

groupVoltageEntry  OBJECT-TYPE
	SYNTAX 	GroupVoltageEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a group voltage measurement."
	INDEX { strappingIndex, 
		groupIndex }
	::= { groupVoltageTable 1 }

GroupVoltageEntry ::= SEQUENCE {
	groupVoltageMeasType
		INTEGER,
	groupVoltage
		Integer32,
	groupVoltageThStatus
		INTEGER,
	groupVoltageThLowerWarning
		Integer32,
	groupVoltageThLowerCritical
		Integer32,
	groupVoltageThUpperWarning
		Integer32,
	groupVoltageThUpperCritical
		Integer32
}

groupVoltageMeasType  OBJECT-TYPE
	SYNTAX     INTEGER {
		unknown (0),
		singlePhase (1),
		phase1toN (2),
		phase2toN (3),
		phase3toN (4),
		phase1to2 (5),
		phase2to3 (6),
		phase3to1 (7)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Value indicates what voltage is being measured in this table row."
	::= { groupVoltageEntry 2 }

groupVoltage  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Units are millivolts."
	::= { groupVoltageEntry 3 }

groupVoltageThStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		lowWarning (1),
		lowCritical (2),
		highWarning (3),
		highCritical (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured group voltage relative to the configured thresholds."
	::= { groupVoltageEntry 4 }

groupVoltageThLowerWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower warning threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { groupVoltageEntry 5 }

groupVoltageThLowerCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower critical threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { groupVoltageEntry 6 }

groupVoltageThUpperWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper warning threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { groupVoltageEntry 7 }

groupVoltageThUpperCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper critical threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { groupVoltageEntry 8 }

groupCurrentTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF GroupCurrentEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of group current measurements.  There can be only one current
		      measurement for each group."
	::= { groups 4 }

groupCurrentEntry  OBJECT-TYPE
	SYNTAX 	GroupCurrentEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a group current measurement."
	INDEX { strappingIndex, 
		groupIndex }
	::= { groupCurrentTable 1 }

GroupCurrentEntry ::= SEQUENCE {
	groupCurrentCapacity
		Integer32,
	groupCurrent
		Integer32,
	groupCurrentThStatus
		INTEGER,
	groupCurrentThLowerWarning
		Integer32,
	groupCurrentThLowerCritical
		Integer32,
	groupCurrentThUpperWarning
		Integer32,
	groupCurrentThUpperCritical
		Integer32,
	groupCurrentCrestFactor
		Integer32,
	groupCurrentPercentLoad
		Integer32
}

groupCurrentCapacity  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Rated current capacity of the group.  Units are milliamps.  A negative 
		      value indicates that the hardware current capacity is unknown (it
		      will always be unknown for custom groups)."
	::= { groupCurrentEntry 2 }

groupCurrent  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"A group current measurement value.  Units are milliamps."
	::= { groupCurrentEntry 3 }

groupCurrentThStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		lowWarning (1),
		lowCritical (2),
		highWarning (3),
		highCritical (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured group current relative to the configured thresholds."
	::= { groupCurrentEntry 4 }

groupCurrentThLowerWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower warning threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { groupCurrentEntry 5 }

groupCurrentThLowerCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower critical threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { groupCurrentEntry 6 }

groupCurrentThUpperWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper warning threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { groupCurrentEntry 7 }

groupCurrentThUpperCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper critical threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { groupCurrentEntry 8 }

groupCurrentCrestFactor  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Current crest factor.  Units are in milli, for example a crest factor of
                  1.414 will be returned as 1414.  A negative value indicates
		          that this object is not available."
	::= { groupCurrentEntry 9 }

groupCurrentPercentLoad  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Current percent load, based on the rated current capacity.  Units are
                  percentage, for example 80% will be returned as 80.  A negative
                  value indicates that this object is not available."
	::= { groupCurrentEntry 10 }

groupPowerTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF GroupPowerEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of group power measurements.  There can be only one power
		      measurement for each group."
	::= { groups 5 }

groupPowerEntry  OBJECT-TYPE
	SYNTAX 	GroupPowerEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a group power measurement."
	INDEX { strappingIndex, 
		groupIndex }
	::= { groupPowerTable 1 }

GroupPowerEntry ::= SEQUENCE {
	groupVA
		Integer32,
	groupWatts
		Integer32,
	groupWh
		Unsigned32,
	groupWhTimer
		UnixTimeStamp,
	groupPowerFactor
		Integer32,
	groupVAR
		Integer32
}

groupVA  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"A group VA value.  Units are VA.  A negative value indicates
		          that this object is not available."
	::= { groupPowerEntry 2 }

groupWatts  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"A group Watts value.  Units are Watts.  A negative value indicates
		          that this object is not available."
	::= { groupPowerEntry 3 }

groupWh  OBJECT-TYPE
	SYNTAX     Unsigned32 (0..4294967295)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Units are Watt-hours.  This object is writable so that it can be reset to 0.  When it is
		written to, the inputWhTotalTimer will be reset to 0 as well."
	::= { groupPowerEntry 4 }

groupWhTimer  OBJECT-TYPE
	SYNTAX     UnixTimeStamp
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Timestamp of when group Watt-hours (groupWh) was last reset."
	::= { groupPowerEntry 5 }

groupPowerFactor  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"A group PF value.  Units are in thousandths, for example a power factor
                  of 0.958 would be returned as 958, and 0.92 would be returned 
		          as 920.  A negative value indicates that this object is not available."
	::= { groupPowerEntry 6 }

groupVAR  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"A group VAR value.  Units are VAR.  A negative value indicates
		          that this object is not available."
	::= { groupPowerEntry 7 }

groupControlTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF GroupControlEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of controllable groups."
	::= { groups 6 }

groupControlEntry  OBJECT-TYPE
	SYNTAX 	GroupControlEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a controllable group."
	INDEX { strappingIndex, 
		groupIndex }
	::= { groupControlTable 1 }

GroupControlEntry ::= SEQUENCE {
	groupControlStatus
		INTEGER,
	groupControlOffCmd
		Integer32,
	groupControlOnCmd
		Integer32,
	groupControlRebootCmd
		Integer32
}

groupControlStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		off (0),
		on (1),
		rebooting (2),
		mixed (3)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Current state of a controlled group.  A value of 'mixed' means that 
		          that the outlets within the group have differing states."
	::= { groupControlEntry 2 }

groupControlOffCmd  OBJECT-TYPE
	SYNTAX     Integer32 (-1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Group-level outlet control command.
		
		Once the command is issued, the outlets in the group will turn Off immediately.
		0-n : Time in seconds until the group command is issued
		-1 : Cancel a pending group-level Off command 
		
		When read, returns -1 if no command is pending, or the current downcount in seconds of a pending command.
		          
		          Certain ePDUs (mainly those with part numbers beginning with IPV or IPC) do not support delayed control
		          commands.  These will respond with an error if a command value of > 0 is written to this object."
	::= { groupControlEntry 3 }

groupControlOnCmd  OBJECT-TYPE
	SYNTAX     Integer32 (-1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Group-level outlet control command.
		
		Once the command is issued, the outlets in the group will turn On immediately.
		0-n : Time in seconds until the group command is issued
		-1 : Cancel a pending group-level On command 
		
		When read, returns -1 if no command is pending, or the current downcount in seconds of a pending command.
		          
		          Certain ePDUs (mainly those with part numbers beginning with IPV or IPC) do not support delayed control
		          commands.  These will respond with an error if a command value of > 0 is written to this object."
	::= { groupControlEntry 4 }

groupControlRebootCmd  OBJECT-TYPE
	SYNTAX     Integer32 (-1..0)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Group-level outlet control command.
		
		          For outlets that are On prior to the Reboot command, they will switch Off immediately when the command is
		          issued, remain Off for outletControlRebootOffTime seconds, and then turn back On.
		          For outlets that are Off prior to the Reboot command, they will turn On after a delay of outletControlRebootOffTime
		          seconds from when the command is issued.
		0-n : Time in seconds until the Reboot command is issued
		-1 : Cancel a pending group-level Reboot command 
		
		When read, returns -1 if no command is pending, or the current downcount in seconds of a pending command.
		          
		          Certain ePDUs (mainly those with part numbers beginning with IPV or IPC) do not support delayed control
		          commands.  These will respond with an error if a command value of > 0 is written to this object."
	::= { groupControlEntry 5 }

outletTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF OutletEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of outlets.  The number of entries is given by outletCount."
	::= { outlets 1 }

outletEntry  OBJECT-TYPE
	SYNTAX 	OutletEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a particular outlet."
	INDEX { strappingIndex, 
		outletIndex }
	::= { outletTable 1 }

OutletEntry ::= SEQUENCE {
	outletIndex
		Integer32,
	outletID
		DisplayString,
	outletName
		OCTET STRING,
	outletParentCount
		Integer32,
	outletType
		INTEGER,
	outletDesignator
		DisplayString,
	outletPhaseID
		INTEGER
}

outletIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..64)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"A unique value for each outlet.  its value ranges from 1 to outletCount."
	::= { outletEntry 1 }

outletID  OBJECT-TYPE
	SYNTAX     DisplayString (SIZE(2..4))
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Alphanumeric designator for the outlet."
	::= { outletEntry 2 }

outletName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(1..31))
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"A descriptive name for the outlet."
	::= { outletEntry 3 }

outletParentCount  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Number of parents for this outlet."
	::= { outletEntry 4 }

outletType  OBJECT-TYPE
	SYNTAX     INTEGER {
		unknown (0),
		iecC13 (1),
		iecC19 (2),
        uk (10),
		french (11),
		schuko (12),
		nema515 (20),
		nema51520 (21),
		nema520 (22),
		nemaL520 (23),
		nemaL530 (24),
		nema615 (25),
		nema620 (26),
		nemaL620 (27),
		nemaL630 (28),
    nemaL715 (29),
    rf203p277 (30),
       sdg300 (31)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"The physical type of outlet."
	::= { outletEntry 5 }

outletDesignator  OBJECT-TYPE
	SYNTAX     DisplayString (SIZE(2..4))
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Alphanumeric physical name for the outlet."
	::= { outletEntry 6 }

outletPhaseID  OBJECT-TYPE
	SYNTAX     INTEGER {
		singlePhase (1),
		phase1toN (2),
		phase2toN (3),
		phase3toN (4),
		phase1to2 (5),
		phase2to3 (6),
		phase3to1 (7),
		phase12N (8),
		phase23N (9),
		phase31N (10),
		phase123 (11),
		phase123N (12)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Value indicates which phases are connected to each outlet in this table row - single phase
		voltage, phase 1 to neutral, phase 2 to neutral, phase 3 to neutral, phase 1 to phase 2,
		phase 2 to phase 3, phase 3 to phase 1, split-phase with phases 1 and 2, split phase 
		with phases 2 and 3, split phase with phases 3 and 1, three-phase delta, and three-phase wye."
	::= { outletEntry 7 }




outletParentTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF OutletParentEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of parents for this outlet.  For example, this table will link
		      to all of the groups that have this outlet as a child."
	::= { outlets 2 }

outletParentEntry  OBJECT-TYPE
	SYNTAX 	OutletParentEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a particular parent."
	INDEX { strappingIndex, 
		outletIndex, 
		outletParentIndex }
	::= { outletParentTable 1 }

OutletParentEntry ::= SEQUENCE {
	outletParentIndex
		Integer32,
	outletParentType
		INTEGER,
	outletParentOID
		OBJECT IDENTIFIER
}

outletParentIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..32)
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A unique value for each parent.  Its value ranges from 1 to outletParentCount."
	::= { outletParentEntry 1 }

outletParentType  OBJECT-TYPE
	SYNTAX     INTEGER {
		unknown (0),
		breaker (1),
		section (2),
		custom (3)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"The type of the parent."
	::= { outletParentEntry 2 }

outletParentOID  OBJECT-TYPE
	SYNTAX     OBJECT IDENTIFIER
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Object ID of a parent object."
	::= { outletParentEntry 3 }

outletVoltageTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF OutletVoltageEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of outlet voltage measurements."
	::= { outlets 3 }

outletVoltageEntry  OBJECT-TYPE
	SYNTAX 	OutletVoltageEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for an outlet voltage measurement."
	INDEX { strappingIndex, 
		outletIndex }
	::= { outletVoltageTable 1 }

OutletVoltageEntry ::= SEQUENCE {
	outletVoltage
		Integer32,
	outletVoltageThStatus
		INTEGER,
	outletVoltageThLowerWarning
		Integer32,
	outletVoltageThLowerCritical
		Integer32,
	outletVoltageThUpperWarning
		Integer32,
	outletVoltageThUpperCritical
		Integer32
}

outletVoltage  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Units are millivolts."
	::= { outletVoltageEntry 2 }

outletVoltageThStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		lowWarning (1),
		lowCritical (2),
		highWarning (3),
		highCritical (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured outlet voltage relative to the configured thresholds."
	::= { outletVoltageEntry 3 }

outletVoltageThLowerWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower warning threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { outletVoltageEntry 4 }

outletVoltageThLowerCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower critical threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { outletVoltageEntry 5 }

outletVoltageThUpperWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper warning threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { outletVoltageEntry 6 }

outletVoltageThUpperCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..500000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper critical threshold.  Units are millivolts.  A negative value indicates
		          that this object is not available."
	::= { outletVoltageEntry 7 }

outletCurrentTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF OutletCurrentEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of outlet current measurements."
	::= { outlets 4 }

outletCurrentEntry  OBJECT-TYPE
	SYNTAX 	OutletCurrentEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for an outlet current measurement."
	INDEX { strappingIndex, 
		outletIndex }
	::= { outletCurrentTable 1 }

OutletCurrentEntry ::= SEQUENCE {
	outletCurrentCapacity
		Integer32,
	outletCurrent
		Integer32,
	outletCurrentThStatus
		INTEGER,
	outletCurrentThLowerWarning
		Integer32,
	outletCurrentThLowerCritical
		Integer32,
	outletCurrentThUpperWarning
		Integer32,
	outletCurrentThUpperCritical
		Integer32,
	outletCurrentCrestFactor
		Integer32,
    outletCurrentPercentLoad
        Integer32
}

outletCurrentCapacity  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Rated current capacity of the outlet.  Units are milliamps.  A negative
        value indicates that the hardware current capacity is unknown."
	::= { outletCurrentEntry 2 }

outletCurrent  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An outlet current measurement value.  Units are milliamps."
	::= { outletCurrentEntry 3 }

outletCurrentThStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		lowWarning (1),
		lowCritical (2),
		highWarning (3),
		highCritical (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured outlet current relative to the configured thresholds. 
		          A negative value indicates that this object is not available."
	::= { outletCurrentEntry 4 }

outletCurrentThLowerWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower warning threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { outletCurrentEntry 5 }

outletCurrentThLowerCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower critical threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { outletCurrentEntry 6 }

outletCurrentThUpperWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper warning threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { outletCurrentEntry 7 }

outletCurrentThUpperCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..100000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper critical threshold.  Units are milliamps.  A negative value indicates
		          that this object is not available."
	::= { outletCurrentEntry 8 }

outletCurrentCrestFactor  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Current crest factor.  Units are in milli, for example a crest factor of
                  1.414 will be returned as 1414.  A negative value indicates
		          that this object is not available."
	::= { outletCurrentEntry 9 }

outletCurrentPercentLoad  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Current percent load, based on the rated current capacity.  Units are
                  percentage, for example 80% will be returned as 80.  A negative
                  value indicates that this object is not available."
	::= { outletCurrentEntry 10 }

outletPowerTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF OutletPowerEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of outlet power measurements."
	::= { outlets 5 }

outletPowerEntry  OBJECT-TYPE
	SYNTAX 	OutletPowerEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for an outlet power measurement."
	INDEX { strappingIndex, 
		outletIndex }
	::= { outletPowerTable 1 }

OutletPowerEntry ::= SEQUENCE {
	outletVA
		Integer32,
	outletWatts
		Integer32,
	outletWh
		Unsigned32,
	outletWhTimer
		UnixTimeStamp,
	outletPowerFactor
		Integer32,
	outletVAR
		Integer32
}

outletVA  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An outlet VA value.  Units are VA.  A negative value indicates
		          that this object is not available."
	::= { outletPowerEntry 2 }

outletWatts  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An outlet Watts value.  Units are Watts.  A negative value indicates
		          that this object is not available."
	::= { outletPowerEntry 3 }

outletWh  OBJECT-TYPE
	SYNTAX     Unsigned32 (0..4294967295)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Units are Watt-hours.  This object is writable so that it can be reset to 0.  When it is
		written to, the inputWhTotalTimer will be reset to 0 as well."
	::= { outletPowerEntry 4 }

outletWhTimer  OBJECT-TYPE
	SYNTAX     UnixTimeStamp
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Timestamp of when outlet Watt-hours (outletWh) was last reset."
	::= { outletPowerEntry 5 }

outletPowerFactor  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An outlet PF value.  Units are in thousandths, for example a power factor
                  of 0.958 would be returned as 958, and 0.92 would be returned 
		          as 920.  A negative value indicates that this object is not available."
	::= { outletPowerEntry 6 }

outletVAR  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"An outlet VAR value.  Units are VAR.  A negative value indicates
		          that this object is not available."
	::= { outletPowerEntry 7 }

outletControlTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF OutletControlEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of controllable outlets."
	::= { outlets 6 }

outletControlEntry  OBJECT-TYPE
	SYNTAX 	OutletControlEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a controllable outlet."
	INDEX { strappingIndex, 
		outletIndex }
	::= { outletControlTable 1 }

OutletControlEntry ::= SEQUENCE {
	outletControlStatus
		INTEGER,
	outletControlOffCmd
		Integer32,
	outletControlOnCmd
		Integer32,
	outletControlRebootCmd
		Integer32,
	outletControlPowerOnState
		INTEGER,
	outletControlSequenceDelay
		Integer32,
	outletControlRebootOffTime
		Integer32,
  outletControlSwitchable
    INTEGER,
  outletControlShutoffDelay
    Integer32
}

outletControlStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		off (0),
		on (1),
		pendingOff (2),
		pendingOn (3)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Current state of a controlled outlet."
	::= { outletControlEntry 2 }

outletControlOffCmd  OBJECT-TYPE
	SYNTAX     Integer32 (-1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Outlet control command.
		
		Once the command is issued, the outlet will turn Off immediately.
		0-n : Time in seconds until the outlet command is issued
		-1 : Cancel a pending outlet Off command 
		
		When read, returns -1 if no command is pending, or the current downcount in seconds of a pending command.
		          
		          Certain ePDUs (mainly those with part numbers beginning with IPV or IPC) do not support delayed control
		          commands.  These will respond with an error if a command value of > 0 is written to this object."
	::= { outletControlEntry 3 }

outletControlOnCmd  OBJECT-TYPE
	SYNTAX     Integer32 (-1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Outlet control command.
		
		Once the command is issued, the outlet will turn On immediately.
		0-n : Time in seconds until the outlet command is issued
		-1 : Cancel a pending outlet On command 
		
		When read, returns -1 if no command is pending, or the current downcount in seconds of a pending command.
		          
		          Certain ePDUs (mainly those with part numbers beginning with IPV or IPC) do not support delayed control
		          commands.  These will respond with an error if a command value of > 0 is written to this object."
	::= { outletControlEntry 4 }

outletControlRebootCmd  OBJECT-TYPE
	SYNTAX     Integer32 (-1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Outlet control command.
		
		          For outlets that are On prior to this Reboot command, they will switch Off immediately when the command is
		          issued, remain Off for outletControlRebootOffTime seconds, and then turn back On.
		          For outlets that are Off prior to the Reboot command, they will turn On after a delay of outletControlRebootOffTime
		          seconds from when the command is issued.
		0-n : Time in seconds until the Reboot command is issued
		-1 : Cancel a pending outlet Reboot command 
		
		When read, returns -1 if no command is pending, or the current downcount in seconds of a pending command.
		          
		          Certain ePDUs (mainly those with part numbers beginning with IPV or IPC) do not support delayed control
		          commands.  These will respond with an error if a command value of > 0 is written to this object."
	::= { outletControlEntry 5 }

outletControlPowerOnState  OBJECT-TYPE
	SYNTAX     INTEGER {
		off (0),
		on (1),
		lastState (2)
	}
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Determines the outlet state when power is applied to the unit.
		0 : not restart at device startup
		1 : should sequence back ON in line with outletControlSequenceTime
		2 : should take the state the outlet had when power was lost.
		If the state was ON, should sequence back ON in line with outletControlSequenceTime."
	::= { outletControlEntry 6 }

outletControlSequenceDelay  OBJECT-TYPE
	SYNTAX     Integer32 (-1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Time delay in seconds from when a Global Sequence On command is issued to
		when the command is executed on this outlet.  This delay is also used as a power-on
		delay. Set to -1 to exclude this outlet from Global Sequence On
		commands."
	::= { outletControlEntry 7 }

outletControlRebootOffTime  OBJECT-TYPE
	SYNTAX     Integer32 (1..99999)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Time delay in seconds that the outlet should remain in the Off state when executing a Reboot command."
	::= { outletControlEntry 8 }

outletControlSwitchable  OBJECT-TYPE
    	SYNTAX 		    INTEGER {
		            switchable (1),
		            notSwitchable (2)
                            }	
    	MAX-ACCESS    read-write
    	STATUS 		    current
    	DESCRIPTION
		"Determines the outlet capability to be controlled On/Off from the communication channels.
		1 : control On/Off enabled
		2 : control On/Off disabled."
    	::= { outletControlEntry 9 }

outletControlShutoffDelay  OBJECT-TYPE
    	SYNTAX 		        Integer32 (-1..99999)		
    	MAX-ACCESS        read-write
    	STATUS 		        current
    	DESCRIPTION
		"Time delay in seconds that could be taken in account before shutting of the outlet.
    An application which need to shutoff properly an outlet will read this parameter first
    then write it to the command outletControlOffCmd."
    	::= { outletControlEntry 10 }


outletGlobalTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF OutletGlobalEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of globlal configuration on all outlets."
	::= { outlets 7 }

outletGlobalEntry  OBJECT-TYPE
	SYNTAX 	OutletGlobalEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a global variable on all outlets."
	INDEX { strappingIndex 
    }
	::= { outletGlobalTable 1 }

OutletGlobalEntry ::= SEQUENCE {
	outletAutomaticShutoff
		INTEGER
}

outletAutomaticShutoff  OBJECT-TYPE
	SYNTAX     INTEGER {
		notApplicable (0),
		keepTheCurrentPosition (1),
		shutoffTheOutlets (2)
	}	
  MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Determines the state of all outlets when the unit is power off:
        0 : not applicable (read only)
        1 : Keep the outlet relays in the current position when the PDU is powered down
        2 : Makes the outlet relays go to the position that shutoffs the outlets when the PDU is powered down"
	::= { outletGlobalEntry 2 }



temperatureTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF TemperatureEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of temperature probe measurements.  The number of entries is
		      given by temperatureCount."
	::= { environmental 1 }

temperatureEntry  OBJECT-TYPE
	SYNTAX 	TemperatureEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a temperature measurement."
	INDEX { strappingIndex, 
		temperatureIndex }
	::= { temperatureTable 1 }

TemperatureEntry ::= SEQUENCE {
	temperatureIndex
		Integer32,
	temperatureName
		OCTET STRING,
	temperatureProbeStatus
		INTEGER,
	temperatureValue
		Integer32,
	temperatureThStatus
		INTEGER,
	temperatureThLowerWarning
		Integer32,
	temperatureThLowerCritical
		Integer32,
	temperatureThUpperWarning
		Integer32,
	temperatureThUpperCritical
		Integer32
}

temperatureIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..2)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"A unique value for each temperature probe measurement.  Its value
		      ranges from 1 to temperatureCount."
	::= { temperatureEntry 1 }

temperatureName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(1..31))
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"A descriptive name for the temperature probe."
	::= { temperatureEntry 2 }

temperatureProbeStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		bad (-1),
		disconnected (0),
		connected (1)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Indicates whether a probe is connected or not."
	::= { temperatureEntry 3 }

temperatureValue  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Units are in tenths of a degree according to the scale specified by
		      temperatureScale (either Fahrenheit or Celsius). Divide by ten to get
		      degrees."
	::= { temperatureEntry 4 }

temperatureThStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		lowWarning (1),
		lowCritical (2),
		highWarning (3),
		highCritical (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured temperature relative to the configured
		      thresholds."
	::= { temperatureEntry 5 }

temperatureThLowerWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..150000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower warning threshold.  Units are tenths of a degree.  A negative value
                  indicates that this object is not available."
	::= { temperatureEntry 6 }

temperatureThLowerCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..150000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower critical threshold.  Units are tenths of a degree.  A negative value
		          indicates that this object is not available."
	::= { temperatureEntry 7 }

temperatureThUpperWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..150000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper warning threshold.  Units are tenths of a degree.  A negative value
                  indicates that this object is not available."
	::= { temperatureEntry 8 }

temperatureThUpperCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..150000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper critical threshold.  Units are tenths of a degree.  A negative value
                  indicates that this object is not available."
	::= { temperatureEntry 9 }

humidityTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF HumidityEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of humidity probe measurements.  The number of entries is
		      given by humidityCount."
	::= { environmental 2 }

humidityEntry  OBJECT-TYPE
	SYNTAX 	HumidityEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a humidity measurement."
	INDEX { strappingIndex, 
		humidityIndex }
	::= { humidityTable 1 }

HumidityEntry ::= SEQUENCE {
	humidityIndex
		Integer32,
	humidityName
		OCTET STRING,
	humidityProbeStatus
		INTEGER,
	humidityValue
		Integer32,
	humidityThStatus
		INTEGER,
	humidityThLowerWarning
		Integer32,
	humidityThLowerCritical
		Integer32,
	humidityThUpperWarning
		Integer32,
	humidityThUpperCritical
		Integer32
}

humidityIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..2)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"A unique value for each humidity probe measurement.  Its value
		      ranges from 1 to humidityCount."
	::= { humidityEntry 1 }

humidityName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(1..31))
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"A descriptive name for the humidity probe."
	::= { humidityEntry 2 }

humidityProbeStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		bad (-1),
		disconnected (0),
		connected (1)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Indicates whether a probe is connected or not."
	::= { humidityEntry 3 }

humidityValue  OBJECT-TYPE
	SYNTAX     Integer32
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Units are tenths of a percent relative humidity.  Divide the value by 10 to get %RH."
	::= { humidityEntry 4 }

humidityThStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		good (0),
		lowWarning (1),
		lowCritical (2),
		highWarning (3),
		highCritical (4)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Status of the measured humidity relative to the configured
		      thresholds."
	::= { humidityEntry 5 }

humidityThLowerWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..1000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower warning threshold.  Units are 0.1 %RH.  A negative value
                  indicates that this object is not available."
	::= { humidityEntry 6 }

humidityThLowerCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..1000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Lower critical threshold.  Units are 0.1 %RH.  A negative value
                  indicates that this object is not available."
	::= { humidityEntry 7 }

humidityThUpperWarning  OBJECT-TYPE
	SYNTAX     Integer32 (-1..1000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper warning threshold.  Units are 0.1 %RH.  A negative value
                  indicates that this object is not available."
	::= { humidityEntry 8 }

humidityThUpperCritical  OBJECT-TYPE
	SYNTAX     Integer32 (-1..1000)
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"Upper critical threshold.  Units are 0.1 %RH.  A negative value
                  indicates that this object is not available."
	::= { humidityEntry 9 }

contactTable  OBJECT-TYPE
	SYNTAX SEQUENCE OF ContactEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"A list of contact sensors.  The number of entries is
		      given by contactCount."
	::= { environmental 3 }

contactEntry  OBJECT-TYPE
	SYNTAX 	ContactEntry
	MAX-ACCESS not-accessible
	STATUS     current
	DESCRIPTION 
		"An entry for a contact sensor"
	INDEX { strappingIndex, 
		contactIndex }
	::= { contactTable 1 }

ContactEntry ::= SEQUENCE {
	contactIndex
		Integer32,
	contactName
		OCTET STRING,
	contactProbeStatus
		INTEGER,
	contactState
		INTEGER
}

contactIndex  OBJECT-TYPE
	SYNTAX     Integer32 (1..3)
	MAX-ACCESS accessible-for-notify
	STATUS     current
	DESCRIPTION 
		"A unique value for each contact sensor.  Its value ranges from 1 to
		      contactCount."
	::= { contactEntry 1 }

contactName  OBJECT-TYPE
	SYNTAX     OCTET STRING (SIZE(1..31))
	MAX-ACCESS read-write
	STATUS     current
	DESCRIPTION 
		"A descriptive name for the contact sensor."
	::= { contactEntry 2 }

contactProbeStatus  OBJECT-TYPE
	SYNTAX     INTEGER {
		bad (-1),
		disconnected (0),
		connected (1)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"Indicates whether a probe is connected or not.
		Will not be returned  if the contact sensor is internal to the ePDU,
		in that case only contactState should be read."
	::= { contactEntry 3 }

contactState  OBJECT-TYPE
	SYNTAX     INTEGER {
		contactBad (-1),
		contactOpen (0),
		contactClosed (1)
	}
	MAX-ACCESS read-only
	STATUS     current
	DESCRIPTION 
		"The state of the contact sensor."
	::= { contactEntry 4 }

eatonEpduCompliances  MODULE-COMPLIANCE
	STATUS     current
	DESCRIPTION 
		"The requirements for conforming to the ePDU MIB."
	MODULE
		MANDATORY-GROUPS { epduRequiredGroup } 
		GROUP epduOptionalGroup
		DESCRIPTION 
		"Different ePDUs will support a subset of the defined objects."
		GROUP epduNotifyGroup
		DESCRIPTION 
		"Different ePDUs will support a subset of the defined notifications."
	::= { conformance 1 }

epduRequiredGroup  OBJECT-GROUP
	OBJECTS { unitName, 
		firmwareVersion }
	STATUS     current
	DESCRIPTION 
		"Minimal objects are required to conform to this MIB."
	::= { objectGroups 1 }

epduOptionalGroup  OBJECT-GROUP
	OBJECTS { clockValue, 
		commInterface, 
		communicationStatus, 
		contactCount, 
		contactIndex, 
		contactName, 
		contactProbeStatus, 
		contactState, 
		groupBreakerStatus, 
		groupChildCount,
		groupChildOID, 
		groupChildType, 
		groupColor, 
		groupControlOnCmd, 
		groupControlOffCmd, 
		groupControlRebootCmd, 
		groupControlStatus, 
		groupCount, 
		groupCurrent, 
		groupCurrentCapacity, 
		groupCurrentCrestFactor, 
		groupCurrentPercentLoad, 
		groupCurrentThLowerCritical, 
		groupCurrentThLowerWarning, 
		groupCurrentThStatus, 
		groupCurrentThUpperCritical, 
		groupCurrentThUpperWarning, 
		groupDesignator, 
		groupID, 
		groupIndex, 
		groupInputIndex, 
		groupName, 
		groupPowerFactor, 
		groupType, 
		groupVA, 
		groupVAR, 
		groupVoltage, 
		groupVoltageMeasType, 
		groupVoltageThLowerCritical, 
		groupVoltageThLowerWarning, 
		groupVoltageThStatus, 
		groupVoltageThUpperCritical, 
		groupVoltageThUpperWarning, 
		groupWatts, 
		groupWh, 
		groupWhTimer, 
		humidityCount, 
		humidityIndex, 
		humidityName, 
		humidityProbeStatus, 
		humidityThLowerCritical, 
		humidityThLowerWarning, 
		humidityThStatus, 
		humidityThUpperCritical, 
		humidityThUpperWarning, 
		humidityValue, 
		inputCount, 
		inputCurrent, 
		inputCurrentCapacity, 
		inputCurrentCount, 
		inputCurrentCrestFactor, 
		inputCurrentIndex, 
		inputCurrentMeasType, 
		inputCurrentPercentLoad, 
		inputCurrentThLowerCritical, 
		inputCurrentThLowerWarning, 
		inputCurrentThStatus, 
		inputCurrentThUpperCritical, 
		inputCurrentThUpperWarning, 
		inputFeedColor,
		inputFeedName,
		inputFrequency, 
		inputFrequencyStatus, 
		inputIndex, 
		inputPhaseDesignator, 
		inputPlugType, 
		inputPowerCapacity, 
		inputPowerCount, 
		inputPowerFactor, 
		inputPowerMeasType, 
		inputTotalPowerFactor,
		inputTotalVA,
		inputTotalVAR,
		inputTotalWatts,
		inputTotalWh,
		inputTotalWhTimer,
		inputType, 
		inputVA, 
		inputVAR, 
		inputVoltage, 
		inputVoltageCount, 
		inputVoltageIndex, 
		inputVoltageMeasType, 
		inputVoltageThLowerCritical, 
		inputVoltageThLowerWarning, 
		inputVoltageThStatus, 
		inputVoltageThUpperCritical, 
		inputVoltageThUpperWarning, 
		inputWatts, 
		inputWh, 
		inputWhTimer, 
		internalStatus, 
		lcdControl,
		outletAutomaticShutoff,
		outletControlSwitchable,
		outletControlShutoffDelay,
		outletControlOffCmd, 
		outletControlOnCmd, 
		outletControlPowerOnState, 
		outletControlRebootCmd, 
		outletControlRebootOffTime, 
		outletControlSequenceDelay, 
		outletControlStatus, 
		outletCount, 
		outletCurrent, 
		outletCurrentCapacity, 
		outletCurrentCrestFactor, 
		outletCurrentPercentLoad,
		outletCurrentThLowerCritical, 
		outletCurrentThLowerWarning, 
		outletCurrentThStatus, 
		outletCurrentThUpperCritical, 
		outletCurrentThUpperWarning, 
		outletDesignator, 
		outletID, 
		outletIndex, 
		outletName, 
		outletParentCount, 
		outletParentOID, 
		outletParentType, 
		outletPhaseID,
		outletPowerFactor, 
		outletType, 
		outletVA, 
		outletVAR, 
		outletVoltage, 
		outletVoltageThLowerCritical, 
		outletVoltageThLowerWarning, 
		outletVoltageThStatus, 
		outletVoltageThUpperCritical, 
		outletVoltageThUpperWarning, 
		outletWatts, 
		outletWh, 
		outletWhTimer, 
		partNumber, 
		productName, 
		serialNumber, 
		strappingIndex, 
		strappingStatus, 
		systemType, 
		temperatureCount, 
		temperatureIndex, 
		temperatureName, 
		temperatureProbeStatus, 
		temperatureScale, 
		temperatureThLowerCritical, 
		temperatureThLowerWarning, 
		temperatureThStatus, 
		temperatureThUpperCritical, 
		temperatureThUpperWarning, 
		temperatureValue, 
		unitControlOffCmd, 
		unitControlOnCmd, 
		unitName, 
		unitsPresent,
		unitType, 
    userName }
	STATUS     current
	DESCRIPTION 
		"Most objects in this MIB are optional."
	::= { objectGroups 2 }

epduNotifyGroup  NOTIFICATION-GROUP
	NOTIFICATIONS { notifyBootUp, 
		notifyCommunicationStatus, 
		notifyContactState, 
		notifyFailedLogin, 
		notifyGroupCurrentThStatus, 
		notifyGroupVoltageThStatus, 
		notifyGroupBreakerStatus, 
		notifyHumidityThStatus, 
		notifyInputCurrentThStatus, 
		notifyInputFrequencyStatus, 
		notifyInputVoltageThStatus, 
		notifyInternalStatus, 
		notifyOutletControlStatus, 
		notifyOutletCurrentThStatus, 
		notifyOutletVoltageThStatus, 
		notifyProbeStatus, 
		notifyStrappingStatus, 
		notifyTemperatureThStatus, 
		notifyTest, 
		notifyUserLogin, 
		notifyUserLogout }
	STATUS     current
	DESCRIPTION 
		"These notifications will be supported depending on the features of the ePDU.
		      Check the web interface for options to turn these notifications on/off.  If 
		      an option is not listed, then the ePDU likely does not support that
		      notification."
	::= { objectGroups 3 }
END


-- This MIB was created using NuDesign Team's Visual MIBuilder (Ver 4.7).

