EATON-SENSOR-MIB DEFINITIONS ::= BEGIN

IMPORTS
    OBJECT-TYPE, NOTIFICATION-TYPE, MODULE-IDENTITY, 
    Counter32, Integer32
        FROM SNMPv2-SMI
    NOTIFICATION-GROUP, OBJECT-GROUP, MODULE-COMPLIANCE
        FROM SNMPv2-CONF
    TEXTUAL-CONVENTION
        FROM SNMPv2-TC
    sensorAgent
        FROM EATON-OIDS;

eatonSensor MODULE-IDENTITY
    LAST-UPDATED "201812171200Z"
    ORGANIZATION 
        "Eaton Corporation"
    CONTACT-INFO 
        "http://powerquality.eaton.com"
    DESCRIPTION 
        "The MIB module for Eaton Sensors."
    REVISION "201812171200Z"
    DESCRIPTION 
        "Initial release."
::= { sensorAgent 1 }

-- eatonSensor { iso org(3) dod(6) internet(1) private(4)
--       enterprises(1) eaton(534) products(6) sensorAgent(8) (1) }

sensor               OBJECT IDENTIFIER ::= { eatonSensor 1 }
temperature          OBJECT IDENTIFIER ::= { eatonSensor 2 }
humidity             OBJECT IDENTIFIER ::= { eatonSensor 3 }
digitalInput         OBJECT IDENTIFIER ::= { eatonSensor 4 }
conformance          OBJECT IDENTIFIER ::= { eatonSensor 10 }

-- Textual Conventions
UnixTimeStamp ::= TEXTUAL-CONVENTION
    DISPLAY-HINT      "dddddddddd"
    STATUS     current
    DESCRIPTION 
        "Unix time stamp. Measured in seconds since January 1, 1970."
    SYNTAX  Counter32

PositionType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the position by reference to the data center aisle."
    SYNTAX  INTEGER {
        undefined(0),
        other(1),
        rackRear(2),
        rackFront(3),
        batteryRoom(4)
        }

ElevationType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the elevation in the rack."
    SYNTAX  INTEGER {
        undefined(0),
        other(1),
        bottom(2),
        middle(3),
        top(4)
        }

CommunicationStatus ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the communication sensor status or probe status."
    SYNTAX  INTEGER {
        unknown(0),
        communicationOK(2),
        communicationLost(3)
        }

ProbeConnectionType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the probe connection to the sensor or probe."
    SYNTAX  INTEGER {
        undefined(0),
        internal(1),
        wired(2),
        wireless(3)
        }

EnableType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes enable/disable."
    SYNTAX  INTEGER {
        disabled(0),
        enabled(1)
        }

AlarmType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the alarm according to a measured value by reference to the triggers."
    SYNTAX  INTEGER {
        good(0),
        lowWarning(1),
        lowCritical(2),
        highWarning(3),
        highCritical(4)
        }

ResetCommandType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Commands a reset."
    SYNTAX  INTEGER {
        none(0),
        reset(1)
        }

PolarityType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the polarity configuration."
    SYNTAX  INTEGER {
        normallyOpened(0),
        normallyClosed(1)
        }

AlarmSeverityType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the alarm severity."
    SYNTAX  INTEGER {
        informationnal(1),
        warning(2),
        critical(3)
        }

AlarmLevelType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the alarm level."
    SYNTAX  INTEGER {
        good(0),
        informationnal(1),
        warning(2),
        critical(3)
        }

StateType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the state of a digital input that depends on its measure
                 and the polrity configuration."
    SYNTAX  INTEGER {
        inactive(0),
        active(1)
        }

TemperatureUnitType ::= TEXTUAL-CONVENTION
    STATUS  current
    DESCRIPTION "Describes the temperature unit used to read/write the temperature data."
    SYNTAX  INTEGER {
        tenthOfDegKelvin(0),
        tenthOfDegCelsius(1),
        tenthOfDegFarhenheit(2)
        }

-- -----------------------------------------------------------------------------

sensorCount  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Number of sensor managed on this device."
    ::= { sensor 1 }

sensorIdentificationTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF SensorIdentificationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of sensor devices identification data.
         The number of entries is given by sensorCount."
    ::= { sensor  2}

sensorIdentificationEntry  OBJECT-TYPE
    SYNTAX     SensorIdentificationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a sensor device identification."
    INDEX { sensorIndex }
    ::= { sensorIdentificationTable 1 }

SensorIdentificationEntry ::= SEQUENCE {
    sensorIndex
        Integer32,
    sensorUuid
        OCTET STRING,
    sensorConnectionType
        ProbeConnectionType,
    sensorAddress
        OCTET STRING,
    sensorMonitoredBy
        OBJECT IDENTIFIER,
    sensorManufacturer
        OCTET STRING,
    sensorModel
        OCTET STRING,
    sensorPartNumber
        OCTET STRING,
    sensorSerialNumber
        OCTET STRING,
    sensorFirmwareVersion
        OCTET STRING
}

sensorIndex  OBJECT-TYPE
    SYNTAX     Integer32 (1..3)
    MAX-ACCESS accessible-for-notify
    STATUS     current
    DESCRIPTION 
        "A unique value for each sensor device.  Its value
         ranges from 1 to sensorCount."
    ::= { sensorIdentificationEntry 1 }

sensorUuid  OBJECT-TYPE
    SYNTAX     OCTET STRING
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "A unique uuid value for each sensor device."
    ::= { sensorIdentificationEntry 2 }

sensorConnectionType  OBJECT-TYPE
    SYNTAX     ProbeConnectionType
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Sensor connection type with the device that monitors it."
    ::= { sensorIdentificationEntry 3 }

sensorAddress  OBJECT-TYPE
    SYNTAX     OCTET STRING
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Depending of the connection implementation : Modbus Slave Id, BT Mac address, ..."
    ::= { sensorIdentificationEntry 4 }

sensorMonitoredBy  OBJECT-TYPE
    SYNTAX     OBJECT IDENTIFIER
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Parent oid device where the sensor is connected to and monitored by."
    ::= { sensorIdentificationEntry 5 }

sensorManufacturer  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "The vendor name of the sensor device."
    ::= { sensorIdentificationEntry 6 }

sensorModel  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "The model name of the sensor device."
    ::= { sensorIdentificationEntry 7 }

sensorPartNumber  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "The catalog part number of the sensor device."
    ::= { sensorIdentificationEntry 8 }

sensorSerialNumber  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "The serial number of the sensor device."
    ::= { sensorIdentificationEntry 9 }

sensorFirmwareVersion  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "The firmware version of the sensor device."
    ::= { sensorIdentificationEntry 10 }


sensorConfigurationTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF SensorConfigurationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of sensor devices configuration data.
         The number of entries is given by sensorCount."
    ::= { sensor 3 }

sensorConfigurationEntry  OBJECT-TYPE
    SYNTAX     SensorConfigurationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a sensor device configuration."
    INDEX { sensorIndex }
    ::= { sensorConfigurationTable 1 }

SensorConfigurationEntry ::= SEQUENCE {
    sensorName
        OCTET STRING,
    sensorLocation
        OCTET STRING,
    sensorPosition
        PositionType,
    sensorElevation
        ElevationType,
    sensorUElevation
        Integer32
}

sensorName  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The friendly name of the sensor device."
    ::= { sensorConfigurationEntry 1 }

sensorLocation  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The location of the sensor device."
    ::= { sensorConfigurationEntry 2 }
  
sensorPosition  OBJECT-TYPE
    SYNTAX     PositionType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The Position by reference to the data center aisle."
    ::= { sensorConfigurationEntry 3 }

sensorElevation  OBJECT-TYPE
    SYNTAX     ElevationType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The Elevation in the rack."
    ::= { sensorConfigurationEntry 4 }
  
sensorUElevation  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The elevation in the rack in count of U position from the bottom."
    ::= { sensorConfigurationEntry 5 }


sensorMonitoringTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF SensorMonitoringEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of sensor devices monitoring data.
         The number of entries is given by sensorCount."
    ::= { sensor 4 }

sensorMonitoringEntry  OBJECT-TYPE
    SYNTAX     SensorMonitoringEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a sensor device monitoring."
    INDEX { sensorIndex }
    ::= { sensorMonitoringTable 1 }

SensorMonitoringEntry ::= SEQUENCE {
    sensorStatus
        CommunicationStatus,
    sensorStatusSince
        UnixTimeStamp,
    sensorTemperatureCount
        Integer32,
    sensorHumidityCount
        Integer32,
    sensorDigitalInputCount
        Integer32,
    sensorAnalogInputCount
        Integer32
}

sensorStatus  OBJECT-TYPE
    SYNTAX     CommunicationStatus
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Indicates how the sensor is communicating or not."
    ::= { sensorMonitoringEntry 1 }

sensorStatusSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the sensor status last change."
    ::= { sensorMonitoringEntry 2 }

sensorTemperatureCount  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Number of temperature probes managed by the sensor device."
    ::= { sensorMonitoringEntry 3 }

sensorHumidityCount  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Number of humidity probes managed by the sensor device."
    ::= { sensorMonitoringEntry 4 }

sensorDigitalInputCount  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Number of digital input probes managed by the sensor device."
    ::= { sensorMonitoringEntry 5 }

sensorAnalogInputCount  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Number of analog input probes managed by the sensor device."
    ::= { sensorMonitoringEntry 6 }

sensorNotification OBJECT IDENTIFIER ::= { sensor 0 }

notifySensorCount  NOTIFICATION-TYPE
    OBJECTS { sensorCount }
    STATUS     current
    DESCRIPTION 
        "Sent whenever the sensor count changes after a discovery or removing 
         from the UI."
    ::= { sensorNotification 1 }

notifySensorStatus  NOTIFICATION-TYPE
    OBJECTS { sensorIndex,
              sensorUuid,
              sensorStatus,
              sensorStatusSince }
    STATUS     current
    DESCRIPTION 
        "Sent whenever the sensor status changes."
    ::= { sensorNotification 2 }

-- -----------------------------------------------------------------------------

temperatureIdentificationTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF TemperatureIdentificationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of temperature probe measurements. the number of entries
         is given by the temperature count."
    ::= { temperature 1 }

temperatureIdentificationEntry  OBJECT-TYPE
    SYNTAX     TemperatureIdentificationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a temperature probe identification."
    INDEX { sensorIndex, temperatureIndex }
    ::= { temperatureIdentificationTable 1 }

TemperatureIdentificationEntry ::= SEQUENCE {
    temperatureIndex
        Integer32,
    temperatureUuid
        OCTET STRING,
    temperatureConnectionType
        ProbeConnectionType
}

temperatureIndex  OBJECT-TYPE
    SYNTAX     Integer32 (1..2)
    MAX-ACCESS accessible-for-notify
    STATUS     current
    DESCRIPTION 
        "A unique value for each temperature probe measurement.  Its value
              ranges from 1 to sensorTemperatureCount."
    ::= { temperatureIdentificationEntry 1 }

temperatureUuid  OBJECT-TYPE
    SYNTAX     OCTET STRING
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "A unique uuid value for each temperature."
    ::= { temperatureIdentificationEntry 2 }

temperatureConnectionType  OBJECT-TYPE
    SYNTAX     ProbeConnectionType
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Probe connection type with the sensor that monitors it."
    ::= { temperatureIdentificationEntry 3 }


temperatureConfigurationTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF TemperatureConfigurationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of temperature probe configuration.  The number of entries is
              given by sensorTemperatureCount."
    ::= { temperature 2 }

temperatureConfigurationEntry  OBJECT-TYPE
    SYNTAX     TemperatureConfigurationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a temperature probe configuration."
    INDEX { sensorIndex, temperatureIndex }
    ::= { temperatureConfigurationTable 1 }

TemperatureConfigurationEntry ::= SEQUENCE {
    temperatureName
        OCTET STRING,
    temperatureEnable
        EnableType,
    temperatureOffset
        Integer32,
    temperatureAlarmEnable
        EnableType,
    temperatureThresholdLowWarning
         Integer32,
    temperatureThresholdLowCritical
         Integer32,
    temperatureThresholdHighWarning
         Integer32,
    temperatureThresholdHighCritical
         Integer32,
    temperatureThresholdHysteresis
         Integer32,
    temperatureAlarmGracePeriod
         Integer32
}

temperatureName  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The friendly name of the sensor temperature probe."
    ::= { temperatureConfigurationEntry 1 }

temperatureEnable  OBJECT-TYPE
    SYNTAX     EnableType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the temperature acquired or not.
         0:disabled, 1:enabled"
    ::= { temperatureConfigurationEntry 2 }

temperatureOffset  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the offset (Minus or Plus) to be added to the acquired value
         in order to correct the probe measurement error.
         See temperatureUnit data for the units."
    ::= { temperatureConfigurationEntry 3 }

temperatureAlarmEnable  OBJECT-TYPE
    SYNTAX     EnableType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the temperature alarm depending on the thresholds evaluated or not.
         0:disabled, 1:enabled"
    ::= { temperatureConfigurationEntry 4 }

temperatureThresholdLowWarning  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Low warning temperature threshold.
         See temperatureUnit data for the units."
    ::= { temperatureConfigurationEntry 5 }

temperatureThresholdLowCritical  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Low critical temperature threshold.
         See temperatureUnit data for the units."
    ::= { temperatureConfigurationEntry 6 }

temperatureThresholdHighWarning  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "High warning temperature threshold.
         See temperatureUnit data for the units."
    ::= { temperatureConfigurationEntry 7 }

temperatureThresholdHighCritical  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "High critical temperature threshold.
         See temperatureUnit data for the units."
    ::= { temperatureConfigurationEntry 8 }

temperatureThresholdHysteresis  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Temperature threshold hysteresis.
         See temperatureUnit data for the units."
    ::= { temperatureConfigurationEntry 9 }

temperatureAlarmGracePeriod  OBJECT-TYPE
    SYNTAX     Integer32 (1..60)
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The grace period the alarm triggers after the acquired value crosses
         a trigger value (in seconds)."
    ::= { temperatureConfigurationEntry 10 }


temperatureMonitoringTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF TemperatureMonitoringEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of temperature probe monitoring.  The number of entries is
         given by sensorTemperatureCount."
    ::= { temperature 3 }

temperatureMonitoringEntry  OBJECT-TYPE
    SYNTAX     TemperatureMonitoringEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a temperature probe monitoring."
    INDEX { sensorIndex, temperatureIndex }
    ::= { temperatureMonitoringTable 1 }

TemperatureMonitoringEntry ::= SEQUENCE {
    temperatureAlarm
         AlarmType,
    temperatureAlarmChangeSince
         UnixTimeStamp,
    temperatureValue
         Integer32,
    temperatureCommunicationStatus
         CommunicationStatus,
    temperatureCommunicationStatusSince
         UnixTimeStamp
}

temperatureAlarm  OBJECT-TYPE
    SYNTAX     AlarmType
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Alarm set according to the realtime measure compared to the thresholds."
    ::= { temperatureMonitoringEntry 1 }

temperatureAlarmChangeSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the temperature alarm last change."
    ::= { temperatureMonitoringEntry 2 }

temperatureValue  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Realtime measured value after correction with the offset.
         See temperatureUnit data for the units."
    ::= { temperatureMonitoringEntry 3 }

temperatureCommunicationStatus  OBJECT-TYPE
    SYNTAX     CommunicationStatus
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Indicates how the temperature probe is communicating or not."
    ::= { temperatureMonitoringEntry 4 }

temperatureCommunicationStatusSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the temperature communication status last change."
    ::= { temperatureMonitoringEntry 5 }


temperatureMonitoringMinMaxTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF TemperatureMonitoringMinMaxEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of temperature probe monitoring Min and Max.  The number of entries is
         given by sensorTemperatureCount."
    ::= { temperature 4 }

temperatureMonitoringMinMaxEntry  OBJECT-TYPE
    SYNTAX     TemperatureMonitoringMinMaxEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a temperature probe monitoring Min and Max."
    INDEX { sensorIndex, temperatureIndex }
    ::= { temperatureMonitoringMinMaxTable 1 }

TemperatureMonitoringMinMaxEntry ::= SEQUENCE {
    temperatureMinValue
         Integer32,
    temperatureMinValueSince
         UnixTimeStamp,
    temperatureMaxValue
         Integer32,
    temperatureMaxValueSince
         UnixTimeStamp,
    temperatureResetMinMax
         ResetCommandType
}

temperatureMinValue  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Minimum value registered since the 1st connection of the sensor or the last reset.
         See temperatureUnit data for the units."
    ::= { temperatureMonitoringMinMaxEntry 1 }

temperatureMinValueSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the temperature min value last change."
    ::= { temperatureMonitoringMinMaxEntry 2 }

temperatureMaxValue  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Maximum value registered since the 1st connection of the sensor or the last reset.
         See temperatureUnit data for the units."
    ::= { temperatureMonitoringMinMaxEntry 3 }

temperatureMaxValueSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the temperature max value last change."
    ::= { temperatureMonitoringMinMaxEntry 4 }

temperatureResetMinMax  OBJECT-TYPE
    SYNTAX     ResetCommandType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Command that resets the min and max data with the current measure.
         0:None, 1:Reset"
    ::= { temperatureMonitoringMinMaxEntry 5 }

temperatureUnit  OBJECT-TYPE
    SYNTAX     TemperatureUnitType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Temperature unit configuration. It is a global setting for all the v1
         and  v3 SNMP client. It does not involve the temperature unit of data
         stored and managed in the card. But it does configure the unit the temperatures
         data are red and written in this Mib.
         The possible values are tenthOfDegCelsius(0), tenthOfDegFarhenheit(1),
         tenthOfDegKelvin(2)."
    ::= { temperature 5 }


temperatureNotification OBJECT IDENTIFIER ::= { temperature 0 }

notifyTemperatureAlarm  NOTIFICATION-TYPE
    OBJECTS { sensorIndex,
              temperatureIndex,
              temperatureUuid,
              temperatureAlarm,
              temperatureAlarmChangeSince,
              temperatureValue }
    STATUS     current
    DESCRIPTION 
        "Sent whenever the temperature alarm changes."
    ::= { temperatureNotification 1 }

notifyTemperatureCommunicationStatus  NOTIFICATION-TYPE
    OBJECTS { sensorIndex,
              temperatureIndex,
              temperatureUuid,
              temperatureCommunicationStatus,
              temperatureCommunicationStatusSince }
    STATUS     current
    DESCRIPTION 
        "Sent whenever the temperature communication status changes.
         Is not implemented when the probe is internal (see temperatureConnectionType)."
    ::= { temperatureNotification 2 }

-- -----------------------------------------------------------------------------


humidityIdentificationTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF HumidityIdentificationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of humidity probe measurements. the number of entries
         is given by the humidity count."
    ::= { humidity 1 }

humidityIdentificationEntry  OBJECT-TYPE
    SYNTAX     HumidityIdentificationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a humidity probe identification."
    INDEX { sensorIndex, humidityIndex }
    ::= { humidityIdentificationTable 1 }

HumidityIdentificationEntry ::= SEQUENCE {
    humidityIndex
        Integer32,
    humidityUuid
        OCTET STRING,
    humidityConnectionType
        ProbeConnectionType
}

humidityIndex  OBJECT-TYPE
    SYNTAX     Integer32 (1..2)
    MAX-ACCESS accessible-for-notify
    STATUS     current
    DESCRIPTION 
        "A unique value for each humidity probe measurement.  Its value
              ranges from 1 to sensorhumidityCount."
    ::= { humidityIdentificationEntry 1 }

humidityUuid  OBJECT-TYPE
    SYNTAX     OCTET STRING
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "A unique uuid value for each humidity."
    ::= { humidityIdentificationEntry 2 }

humidityConnectionType  OBJECT-TYPE
    SYNTAX     ProbeConnectionType
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Probe connection type with the sensor that monitors it."
    ::= { humidityIdentificationEntry 3 }


humidityConfigurationTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF HumidityConfigurationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of humidity probe configuration.  The number of entries is
              given by sensorhumidityCount."
    ::= { humidity 2 }

humidityConfigurationEntry  OBJECT-TYPE
    SYNTAX     HumidityConfigurationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a humidity probe configuration."
    INDEX { sensorIndex, humidityIndex }
    ::= { humidityConfigurationTable 1 }

HumidityConfigurationEntry ::= SEQUENCE {
    humidityName
        OCTET STRING,
    humidityEnable
        EnableType,
    humidityOffset
        Integer32,
    humidityAlarmEnable
        EnableType,
    humidityThresholdLowWarning
         Integer32,
    humidityThresholdLowCritical
         Integer32,
    humidityThresholdHighWarning
         Integer32,
    humidityThresholdHighCritical
         Integer32,
    humidityThresholdHysteresis
         Integer32,
    humidityAlarmGracePeriod
         Integer32
}

humidityName  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The friendly name of the sensor humidity probe."
    ::= { humidityConfigurationEntry 1 }

humidityEnable  OBJECT-TYPE
    SYNTAX     EnableType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the humidity acquired or not.
         0:disabled, 1:enabled"
    ::= { humidityConfigurationEntry 2 }

humidityOffset  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the offset (Minus or Plus) to be added to the acquired value
         in order to correct the probe measurement error. in tenth of % units."
    ::= { humidityConfigurationEntry 3 }

humidityAlarmEnable  OBJECT-TYPE
    SYNTAX     EnableType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the humidity alarm depending on the thresholds evaluated or not.
         0:disabled, 1:enabled"
    ::= { humidityConfigurationEntry 4 }

humidityThresholdLowWarning  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Low warning humidity threshold in tenth of % units."
    ::= { humidityConfigurationEntry 5 }

humidityThresholdLowCritical  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Low critical humidity threshold in tenth of % units."
    ::= { humidityConfigurationEntry 6 }

humidityThresholdHighWarning  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "High warning humidity threshold in tenth of % units."
    ::= { humidityConfigurationEntry 7 }

humidityThresholdHighCritical  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "High critical humidity threshold in tenth of % units."
    ::= { humidityConfigurationEntry 8 }

humidityThresholdHysteresis  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "humidity threshold hysteresis in tenth of % units."
    ::= { humidityConfigurationEntry 9 }

humidityAlarmGracePeriod  OBJECT-TYPE
    SYNTAX     Integer32 (1..60)
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The grace period the alarm triggers after the acquired value crosses
         a trigger value (in seconds)."
    ::= { humidityConfigurationEntry 10 }


humidityMonitoringTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF HumidityMonitoringEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of humidity probe monitoring.  The number of entries is
         given by sensorhumidityCount."
    ::= { humidity 3 }

humidityMonitoringEntry  OBJECT-TYPE
    SYNTAX     HumidityMonitoringEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a humidity probe monitoring."
    INDEX { sensorIndex, humidityIndex }
    ::= { humidityMonitoringTable 1 }

HumidityMonitoringEntry ::= SEQUENCE {
    humidityAlarm
         AlarmType,
    humidityAlarmChangeSince
         UnixTimeStamp,
    humidityValue
         Integer32,
    humidityCommunicationStatus
         CommunicationStatus,
    humidityCommunicationStatusSince
         UnixTimeStamp
}

humidityAlarm  OBJECT-TYPE
    SYNTAX     AlarmType
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Alarm set according to the realtime measure compared to the thresholds."
    ::= { humidityMonitoringEntry 1 }

humidityAlarmChangeSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the humidity alarm last change."
    ::= { humidityMonitoringEntry 2 }

humidityValue  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Realtime measured value after correction with the offset. in tenth of % units."
    ::= { humidityMonitoringEntry 3 }

humidityCommunicationStatus  OBJECT-TYPE
    SYNTAX     CommunicationStatus
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Indicates how the humidity probe is communicating or not."
    ::= { humidityMonitoringEntry 4 }

humidityCommunicationStatusSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the humidity communication status last change."
    ::= { humidityMonitoringEntry 5 }


humidityMonitoringMinMaxTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF HumidityMonitoringMinMaxEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of humidity probe monitoring Min and Max.  The number of entries is
         given by sensorhumidityCount."
    ::= { humidity 4 }

humidityMonitoringMinMaxEntry  OBJECT-TYPE
    SYNTAX     HumidityMonitoringMinMaxEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a humidity probe monitoring Min and Max."
    INDEX { sensorIndex, humidityIndex }
    ::= { humidityMonitoringMinMaxTable 1 }

HumidityMonitoringMinMaxEntry ::= SEQUENCE {
    humidityMinValue
         Integer32,
    humidityMinValueSince
         UnixTimeStamp,
    humidityMaxValue
         Integer32,
    humidityMaxValueSince
         UnixTimeStamp,
    humidityResetMinMax
         ResetCommandType
}

humidityMinValue  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Minimum value registered since the 1st connection of the sensor or the last reset.
         in tenth of % units."
    ::= { humidityMonitoringMinMaxEntry 1 }

humidityMinValueSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the humidity min value last change."
    ::= { humidityMonitoringMinMaxEntry 2 }

humidityMaxValue  OBJECT-TYPE
    SYNTAX     Integer32
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Maximum value registered since the 1st connection of the sensor or the last reset.
         in tenth of % units."
    ::= { humidityMonitoringMinMaxEntry 3 }

humidityMaxValueSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the humidity max value last change."
    ::= { humidityMonitoringMinMaxEntry 4 }

humidityResetMinMax  OBJECT-TYPE
    SYNTAX     ResetCommandType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Command that resets the min and max data with the current measure.
         0:None, 1:Reset"
    ::= { humidityMonitoringMinMaxEntry 5 }


humidityNotification OBJECT IDENTIFIER ::= { humidity 0 }

notifyHumidityAlarm  NOTIFICATION-TYPE
    OBJECTS { sensorIndex,
              humidityIndex,
              humidityUuid,
              humidityAlarm,
              humidityAlarmChangeSince,
              humidityValue }
    STATUS     current
    DESCRIPTION 
        "Sent whenever the humidity alarm changes."
    ::= { humidityNotification 1 }

notifyHumidityCommunicationStatus  NOTIFICATION-TYPE
    OBJECTS { sensorIndex,
              humidityIndex,
              humidityUuid,
              humidityCommunicationStatus,
              humidityCommunicationStatusSince }
    STATUS     current
    DESCRIPTION 
        "Sent whenever the humidity communication status changes.
         Is not implemented when the probe is internal (see humidityConnectionType)."
    ::= { humidityNotification 2 }

-- -----------------------------------------------------------------------------


digitalInputIdentificationTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF DigitalInputIdentificationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of digital input probe measurements.  The number of entries is
              given by sensorDigitalInputCount."
    ::= { digitalInput 1 }

digitalInputIdentificationEntry  OBJECT-TYPE
    SYNTAX     DigitalInputIdentificationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a digital input identification."
    INDEX { sensorIndex, digitalInputIndex }
    ::= { digitalInputIdentificationTable 1 }

DigitalInputIdentificationEntry ::= SEQUENCE {
    digitalInputIndex
        Integer32,
    digitalInputUuid
        OCTET STRING,
    digitalInputConnectionType
        ProbeConnectionType
}

digitalInputIndex  OBJECT-TYPE
    SYNTAX     Integer32 (1..2)
    MAX-ACCESS accessible-for-notify
    STATUS     current
    DESCRIPTION 
        "A unique value for each digital input probe measurement.  Its value
              ranges from 1 to sensorDigitalInputCount."
    ::= { digitalInputIdentificationEntry 1 }

digitalInputUuid  OBJECT-TYPE
    SYNTAX     OCTET STRING
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "A unique uuid value for each digital Input."
    ::= { digitalInputIdentificationEntry 2 }

digitalInputConnectionType  OBJECT-TYPE
    SYNTAX     ProbeConnectionType
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Probe connection type with the sensor that monitors it."
    ::= { digitalInputIdentificationEntry 3 }


digitalInputConfigurationTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF DigitalInputConfigurationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of digital input probe configuration.  The number of entries is
              given by sensorDigitalInputCount."
    ::= { digitalInput 2 }

digitalInputConfigurationEntry  OBJECT-TYPE
    SYNTAX     DigitalInputConfigurationEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a digital input probe configuration."
    INDEX { sensorIndex, digitalInputIndex }
    ::= { digitalInputConfigurationTable 1 }

DigitalInputConfigurationEntry ::= SEQUENCE {
    digitalInputName
        OCTET STRING,
    digitalInputEnable
        EnableType,
    digitalInputPolarity
        PolarityType,
    digitalInputAlarmEnable
        EnableType,
    digitalInputAlarmSeverity
        AlarmSeverityType,
    digitalInputAlarmGracePeriod
        Integer32
}

digitalInputName  OBJECT-TYPE
    SYNTAX     OCTET STRING (SIZE(1..31))
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The friendly name of the digital input probe."
    ::= { digitalInputConfigurationEntry 1 }

digitalInputEnable  OBJECT-TYPE
    SYNTAX     EnableType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the digital input acquired or not.
         0:disabled, 1:enabled"
    ::= { digitalInputConfigurationEntry 2 }

digitalInputPolarity  OBJECT-TYPE
    SYNTAX     PolarityType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the digitalInput polarity.
        0 : Normally opened, 1 : Normally closed"
    ::= { digitalInputConfigurationEntry 3 }

digitalInputAlarmEnable  OBJECT-TYPE
    SYNTAX     EnableType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the digitalInput alarm depending on the polarity evaluated or not.
         0:disabled, 1:enabled"
    ::= { digitalInputConfigurationEntry 4 }

digitalInputAlarmSeverity  OBJECT-TYPE
    SYNTAX     AlarmSeverityType
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "Configure the alarm severity."
    ::= { digitalInputConfigurationEntry 5 }

digitalInputAlarmGracePeriod  OBJECT-TYPE
    SYNTAX     Integer32 (1..60)
    MAX-ACCESS read-write
    STATUS     current
    DESCRIPTION 
        "The delay the alarm triggers when the state change event occurs (in seconds)."
    ::= { digitalInputConfigurationEntry 6 }


digitalInputMonitoringTable  OBJECT-TYPE
    SYNTAX SEQUENCE OF DigitalInputMonitoringEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "A list of digital input probee monitoring.  The number of entries is
         given by sensorDigitalInputCount."
    ::= { digitalInput 3 }

digitalInputMonitoringEntry  OBJECT-TYPE
    SYNTAX     DigitalInputMonitoringEntry
    MAX-ACCESS not-accessible
    STATUS     current
    DESCRIPTION 
        "An entry for a digital Input probe."
    INDEX { sensorIndex, digitalInputIndex }
    ::= { digitalInputMonitoringTable 1 }

DigitalInputMonitoringEntry ::= SEQUENCE {
    digitalInputAlarm
         AlarmLevelType,
    digitalInputAlarmChangeSince
         UnixTimeStamp,
    digitalInputState
         Integer32,
    digitalInputStateSince
         UnixTimeStamp,
    digitalInputCommunicationStatus
         CommunicationStatus,
    digitalInputCommunicationStatusSince
         UnixTimeStamp
}

digitalInputAlarm  OBJECT-TYPE
    SYNTAX     AlarmLevelType
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Alarm set according to the polarity and alarm severity configuration."
    ::= { digitalInputMonitoringEntry 1 }

digitalInputAlarmChangeSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the digital input alarm last change."
    ::= { digitalInputMonitoringEntry 2 }

digitalInputState  OBJECT-TYPE
    SYNTAX     StateType
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Measure of the digital input after applying the polarity configured.
         0 : Inactive, 1 : Active"
    ::= { digitalInputMonitoringEntry 3 }

digitalInputStateSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the digital input state last change."
    ::= { digitalInputMonitoringEntry 4 }

digitalInputCommunicationStatus  OBJECT-TYPE
    SYNTAX     CommunicationStatus
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "Indicates how the digital input is communicating or not."
    ::= { digitalInputMonitoringEntry 5 }

digitalInputCommunicationStatusSince  OBJECT-TYPE
    SYNTAX     UnixTimeStamp
    MAX-ACCESS read-only
    STATUS     current
    DESCRIPTION 
        "UTC time in seconds since 1970/01/01 dating the digital input communication status last change."
    ::= { digitalInputMonitoringEntry 6 }


digitalInputNotification OBJECT IDENTIFIER ::= { digitalInput 0 }

notifyDigitalInputAlarm  NOTIFICATION-TYPE
    OBJECTS { sensorIndex,
              digitalInputIndex,
              digitalInputUuid,
              digitalInputAlarm,
              digitalInputAlarmChangeSince,
              digitalInputState,
              digitalInputStateSince }
    STATUS     current
    DESCRIPTION 
        "Sent whenever the digital input alarm changes."
    ::= { digitalInputNotification 1 }

notifydigitalInputCommunicationStatus  NOTIFICATION-TYPE
    OBJECTS { sensorIndex,
              digitalInputIndex,
              digitalInputUuid,
              digitalInputCommunicationStatus,
              digitalInputCommunicationStatusSince }
    STATUS     current
    DESCRIPTION 
        "Sent whenever the digital input communication status changes.
         Is not implemented when the probe is internal (see digitalInputConnectionType)."
    ::= { digitalInputNotification 2 }


eatonSensorCompliances  MODULE-COMPLIANCE
    STATUS     current
    DESCRIPTION 
        "The requirements for conforming to the Sensor MIB."
    MODULE
        MANDATORY-GROUPS { sensorRequiredGroup } 
        GROUP sensorOptionalGroup
        DESCRIPTION 
        "Different sensors will support a subset of the defined objects."
        GROUP sensorNotifyGroup
        DESCRIPTION 
        "Different sensors will support a subset of the defined notifications."
    ::= { conformance 1 }

objectGroups         OBJECT IDENTIFIER ::= { conformance 2 }

sensorRequiredGroup  OBJECT-GROUP
    OBJECTS { sensorCount,
              sensorIndex,
              sensorManufacturer,
              sensorModel,
              sensorPartNumber,
              sensorSerialNumber,
              sensorFirmwareVersion,
              sensorName,
              sensorStatus,
              sensorStatusSince,
              sensorTemperatureCount,
              sensorHumidityCount,
              sensorDigitalInputCount,
              temperatureIndex,
              temperatureName,
              temperatureValue,
              temperatureUnit,
              humidityIndex,
              humidityName,
              humidityValue,
              digitalInputIndex,
              digitalInputName
            }
    STATUS     current
    DESCRIPTION 
        "These objects are required to conform to this MIB."
    ::= { objectGroups 1 }

sensorOptionalGroup  OBJECT-GROUP
    OBJECTS { sensorUuid,
              sensorConnectionType,
              sensorAddress,
              sensorMonitoredBy,
              sensorLocation,
              sensorPosition,
              sensorElevation,
              sensorUElevation,
              sensorAnalogInputCount,
              temperatureUuid,
              temperatureConnectionType,
              temperatureEnable,
              temperatureOffset,
              temperatureAlarmEnable,                                                 
              temperatureThresholdLowWarning,
              temperatureThresholdLowCritical,
              temperatureThresholdHighWarning,
              temperatureThresholdHighCritical,
              temperatureThresholdHysteresis,
              temperatureAlarmGracePeriod,
              temperatureAlarm,
              temperatureAlarmChangeSince,
              temperatureCommunicationStatus,
              temperatureCommunicationStatusSince,
              temperatureMinValue,
              temperatureMinValueSince,
              temperatureMaxValue,
              temperatureMaxValueSince,
              temperatureResetMinMax,
              humidityUuid,
              humidityConnectionType,
              humidityEnable,
              humidityOffset,
              humidityAlarmEnable,                                                 
              humidityThresholdLowWarning,
              humidityThresholdLowCritical,
              humidityThresholdHighWarning,
              humidityThresholdHighCritical,
              humidityThresholdHysteresis,
              humidityAlarmGracePeriod,
              humidityAlarm,
              humidityAlarmChangeSince,
              humidityCommunicationStatus,
              humidityCommunicationStatusSince,
              humidityMinValue,
              humidityMinValueSince,
              humidityMaxValue,
              humidityMaxValueSince,
              humidityResetMinMax,
              digitalInputUuid,
              digitalInputConnectionType,
              digitalInputEnable,
              digitalInputPolarity,
              digitalInputAlarmEnable,                                                 
              digitalInputAlarmSeverity,
              digitalInputAlarmGracePeriod,
              digitalInputState,
              digitalInputStateSince,
              digitalInputAlarm,
              digitalInputAlarmChangeSince,
              digitalInputCommunicationStatus,
              digitalInputCommunicationStatusSince
         }
    STATUS     current
    DESCRIPTION 
        "These objects in this MIB are optional."
    ::= { objectGroups 2 }

sensorNotifyGroup  NOTIFICATION-GROUP
    NOTIFICATIONS { notifySensorStatus,
                    notifySensorCount,
                    notifyTemperatureAlarm,
                    notifyTemperatureCommunicationStatus,
                    notifyHumidityAlarm,
                    notifyHumidityCommunicationStatus,
                    notifyDigitalInputAlarm,
                    notifydigitalInputCommunicationStatus
         }
    STATUS     current
    DESCRIPTION 
        "These notifications will be supported depending on the features of the sensor."
    ::= { objectGroups 3 }


END
